INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34057','20','1.3.6.1.2.1.2.2.1.19.{#SNMPINDEX}','10392','Interface {#IFNAME}({#IFALIAS}): Outbound packets discarded','net.if.out.discards[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The number of outbound packets which were chosen to be discarded
even though no errors had been detected to prevent their being deliverable to a higher-layer protocol.
One possible reason for discarding such a packet could be to free up buffer space.
Discontinuities in the value of this counter can occur at re-initialization of the management system,
and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6afb99d2489a4e4fa6ed329d3b140e99','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS DISCARDED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34058','20','1.3.6.1.2.1.2.2.1.20.{#SNMPINDEX}','10392','Interface {#IFNAME}({#IFALIAS}): Outbound packets with errors','net.if.out.errors[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
For packet-oriented interfaces, the number of outbound packets that contained errors preventing them from being deliverable to a higher-layer protocol.  For character-oriented or fixed-length interfaces, the number of outbound transmission units that contained errors preventing them from being deliverable to a higher-layer protocol. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b58d6657f5e14788829ff03f04bd1ac9','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS WITH ERRORS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34059','20','1.3.6.1.2.1.31.1.1.1.10.{#SNMPINDEX}','10392','Interface {#IFNAME}({#IFALIAS}): Bits sent','net.if.out[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The total number of octets transmitted out of the interface, including framing characters. This object is a 64-bit version of ifOutOctets.Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fc23b72b6e0c4b0a9d5c9828f25cc43b','INTERFACE {#IFNAME}({#IFALIAS}): BITS SENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34060','20','1.3.6.1.2.1.31.1.1.1.15.{#SNMPINDEX}','10392','Interface {#IFNAME}({#IFALIAS}): Speed','net.if.speed[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
An estimate of the interface''s current bandwidth in units of 1,000,000 bits per second. If this object reports a value of `n'' then the speed of the interface is somewhere in the range of `n-500,000'' to`n+499,999''.  For interfaces which do not vary in bandwidth or for those where no accurate estimation can be made, this object should contain the nominal bandwidth. For a sub-layer which has no concept of bandwidth, this object should be zero.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a69f1d2e284a4d468d7226a68560405f','INTERFACE {#IFNAME}({#IFALIAS}): SPEED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34061','20','1.3.6.1.2.1.2.2.1.8.{#SNMPINDEX}','10392','Interface {#IFNAME}({#IFALIAS}): Operational status','net.if.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'244','','','0','','','','','2',NULL,'MIB: IF-MIB
The current operational state of the interface.
- The testing(3) state indicates that no operational packet scan be passed
- If ifAdminStatus is down(2) then ifOperStatus should be down(2)
- If ifAdminStatus is changed to up(1) then ifOperStatus should change to up(1) if the interface is ready to transmit and receive network traffic
- It should change todormant(5) if the interface is waiting for external actions (such as a serial line waiting for an incoming connection)
- It should remain in the down(2) state if and only if there is a fault that prevents it from going to the up(1) state
- It should remain in the notPresent(6) state if the interface has missing(typically, hardware) components.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9a2539d5137645cc868d80c6543b2a32','INTERFACE {#IFNAME}({#IFALIAS}): OPERATIONAL STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34062','20','1.3.6.1.2.1.2.2.1.3.{#SNMPINDEX}','10392','Interface {#IFNAME}({#IFALIAS}): Interface type','net.if.type[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'245','','','0','','','','','2',NULL,'MIB: IF-MIB
The type of interface.
Additional values for ifType are assigned by the Internet Assigned Numbers Authority (IANA),
through updating the syntax of the IANAifType textual convention.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f286f2bafa3e4d17a74842fff0a86dcf','INTERFACE {#IFNAME}({#IFALIAS}): INTERFACE TYPE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34063','20','1.3.6.1.2.1.10.7.2.1.19.{#SNMPINDEX}','10392','Interface {#IFNAME}({#IFALIAS}): Duplex status','net.if.duplex[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'243','','','0','','','','','2',NULL,'MIB: EtherLike-MIB
Object name: dot3StatsDuplexStatus
The current mode of operation of the MAC
entity.  ''unknown'' indicates that the current
duplex mode could not be determined.

Management control of the duplex mode is
accomplished through the MAU MIB.  When
an interface does not support autonegotiation,
or when autonegotiation is not enabled, the
duplex mode is controlled using
ifMauDefaultType.  When autonegotiation is
supported and enabled, duplex mode is controlled
using ifMauAutoNegAdvertisedBits.  In either
case, the currently operating duplex mode is
reflected both in this object and in ifMauType.

Note that this object provides redundant
information with ifMauType.  Normally, redundant
objects are discouraged.  However, in this
instance, it allows a management application to
determine the duplex status of an interface
without having to know every possible value of
ifMauType.  This was felt to be sufficiently
valuable to justify the redundancy.
Reference: [IEEE 802.3 Std.], 30.3.1.1.32,aDuplexStatus.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ab70998b12124fee93168b5e8222512e','INTERFACE {#IFNAME}({#IFALIAS}): DUPLEX STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34064','20','1.3.6.1.4.1.9.9.13.1.5.1.3.{#SNMPINDEX}','10392','{#SNMPVALUE}: Power supply status','sensor.psu.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'242','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonSupplyState','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a3617fa8711146a0bdddd2e721cedb52','{#SNMPVALUE}: POWER SUPPLY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34065','20','1.3.6.1.4.1.9.9.13.1.3.1.6.{#SNMPINDEX}','10392','{#SNMPVALUE}: Temperature status','sensor.temp.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'242','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonTemperatureState
The current state of the test point being instrumented.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e1636ece86b1427cad01e7223052b526','{#SNMPVALUE}: TEMPERATURE STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34066','20','1.3.6.1.4.1.9.9.13.1.3.1.3.{#SNMPINDEX}','10392','{#SNMPVALUE}: Temperature','sensor.temp.value[{#SNMPINDEX}]','1m','7d','365d','0','0','','°C','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonTemperatureValue
The current measurement of the test point being instrumented.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','16a4c905660349aaaddf52573916e187','{#SNMPVALUE}: TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34067','3','','10393','ICMP ping','icmpping','1m','7d','365d','0','3','','','','',NULL,'252','','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d729b3a06df94b6890fe4c62f8d26f60','ICMP PING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34068','3','','10393','ICMP loss','icmppingloss','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3a6fdbfbbf7c4944a24e22e93aabf0e3','ICMP LOSS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34069','3','','10393','ICMP response time','icmppingsec','1m','7d','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','80efc7d77e314e97953cc75b5ae43e92','ICMP RESPONSE TIME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34070','17','','10393','SNMP traps (fallback)','snmptrap.fallback','1m','7d','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'Item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2c44173959284d7db1d2a745c68fa0a3','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34071','20','1.3.6.1.2.1.1.4.0','10393','System contact details','system.contact','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed node, together with information on how to contact this person.  If no contact information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b3ac05facd4349fc8e573525f3fdb239','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34072','20','1.3.6.1.2.1.1.1.0','10393','System description','system.descr','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f21c4e4de69342a68ca060a52fe071d6','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34073','20','1.3.6.1.2.1.47.1.1.1.1.13.1','10393','Hardware model name','system.hw.model','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: ENTITY-MIB','29','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2a0f9c29094f4a72ab66813c931d35ee','HARDWARE MODEL NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34074','20','1.3.6.1.2.1.47.1.1.1.1.11.1','10393','Hardware serial number','system.hw.serialnumber','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: ENTITY-MIB','8','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','487fc626eb5e4629a0585210153ebbd1','HARDWARE SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34075','20','1.3.6.1.2.1.1.6.0','10393','System location','system.location','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet, 3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','679e63af2b3548c48b278da7356ae8ed','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34076','20','1.3.6.1.2.1.1.5.0','10393','System name','system.name','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
An administratively-assigned name for this managed node.By convention, this is the node''s fully-qualified domain name.  If the name is unknown, the value is the zero-length string.','3','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5d51ca0ffadf4e4599390aa9a4644426','SYSTEM NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34077','20','1.3.6.1.2.1.1.2.0','10393','System object ID','system.objectid','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management subsystem contained in the entity.  This value is allocated within the SMI enterprises subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1 to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2d49036582724a19b5cd5006360be8d2','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34078','20','1.3.6.1.2.1.1.1.0','10393','Operating system','system.sw.os','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB','5','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5852aecfbfbe429097c660d8a1ce47ee','OPERATING SYSTEM');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34079','20','1.3.6.1.2.1.1.3.0','10393','Uptime (network)','system.net.uptime','1m','7d','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','54ff117dbac14916aee823e247bff23f','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34080','5','','10393','SNMP agent availability','zabbix[host,snmp,available]','1m','7d','365d','0','3','','','','',NULL,'253','','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','642cee0c23134982adc4dfc486a63843','SNMP AGENT AVAILABILITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34081','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.109.1.1.1.1.5]','10393','CPU discovery','cpu.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'If your IOS device has several CPUs, you must use CISCO-PROCESS-MIB and its object cpmCPUTotal5minRev from the table called cpmCPUTotalTable ,
indexed with cpmCPUTotalIndex .
This table allows CISCO-PROCESS-MIB to keep CPU statistics for different physical entities in the router,
like different CPU chips, group of CPUs, or CPUs in different modules/cards.
In case of a single CPU, cpmCPUTotalTable has only one entry.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a55dd3dac1d74fdea664fbccbce717cc','CPU DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34082','20','discovery[{#ENT_CLASS},1.3.6.1.2.1.47.1.1.1.1.5,{#ENT_NAME},1.3.6.1.2.1.47.1.1.1.1.7,{#ENT_SN},1.3.6.1.2.1.47.1.1.1.1.11]','10393','Entity Serial Numbers discovery','entity_sn.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7361d8c6f2a34111b478f4d5c1e12d01','ENTITY SERIAL NUMBERS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34083','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.13.1.4.1.2]','10393','FAN discovery','fan.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The table of fan status maintained by the environmental monitor.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a13d58f913b24056bc2f0e770657d1be','FAN DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34084','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.48.1.1.1.2]','10393','Memory discovery','memory.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of ciscoMemoryPoolTable, a table of memory pool monitoring entries.
http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15216-contiguous-memory.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','637a377b92854de1a0c05f53a2a88851','MEMORY DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34085','20','discovery[{#IFOPERSTATUS},1.3.6.1.2.1.2.2.1.8,{#IFADMINSTATUS},1.3.6.1.2.1.2.2.1.7,{#IFALIAS},1.3.6.1.2.1.31.1.1.1.18,{#IFNAME},1.3.6.1.2.1.31.1.1.1.1,{#IFDESCR},1.3.6.1.2.1.2.2.1.2,{#IFTYPE},1.3.6.1.2.1.2.2.1.3]','10393','Network interfaces discovery','net.if.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovering interfaces from IF-MIB.','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','11a26fe1c76447ba82250c7056c3ff9f','NETWORK INTERFACES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34086','20','discovery[{#SNMPVALUE},1.3.6.1.2.1.10.7.2.1.19,{#IFOPERSTATUS},1.3.6.1.2.1.2.2.1.8,{#IFALIAS},1.3.6.1.2.1.31.1.1.1.18,{#IFNAME},1.3.6.1.2.1.31.1.1.1.1,{#IFDESCR},1.3.6.1.2.1.2.2.1.2]','10393','EtherLike discovery','net.if.duplex.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovering interfaces from IF-MIB and EtherLike-MIB. Interfaces with up(1) Operational Status are discovered.','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','51398634ec1742dc95df5907e1042763','ETHERLIKE DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34087','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.13.1.5.1.2]','10393','PSU discovery','psu.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The table of power supply status maintained by the environmental monitor card.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','60431e4af4764ee694973a0ed13b2898','PSU DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34088','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.13.1.3.1.2]','10393','Temperature discovery','temperature.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of ciscoEnvMonTemperatureTable (ciscoEnvMonTemperatureDescr), a table of ambient temperature status
maintained by the environmental monitor.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','84a4865dabb8489a9981eb02de238837','TEMPERATURE DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34089','20','1.3.6.1.4.1.9.9.109.1.1.1.1.8.{#SNMPINDEX}','10393','#{#SNMPINDEX}: CPU utilization','system.cpu.util[{#SNMPINDEX}]','5m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-PROCESS-MIB
Object name: cpmCPUTotal5minRev
The cpmCPUTotal5minRev MIB object provides a more accurate view of the performance of the router over time than the MIB objects cpmCPUTotal1minRev and cpmCPUTotal5secRev . These MIB objects are not accurate because they look at CPU at one minute and five second intervals, respectively. These MIBs enable you to monitor the trends and plan the capacity of your network. The recommended baseline rising threshold for cpmCPUTotal5minRev is 90 percent. Depending on the platform, some routers that run at 90 percent, for example, 2500s, can exhibit performance degradation versus a high-end router, for example, the 7500 series, which can operate fine.
Reference: http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15215-collect-cpu-util-snmp.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','dfb4e2bee3754f6489ee1b5bff628a4d','#{#SNMPINDEX}: CPU UTILIZATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34090','20','1.3.6.1.2.1.47.1.1.1.1.11.{#SNMPINDEX}','10393','{#ENT_NAME}: Hardware serial number','system.hw.serialnumber[{#SNMPINDEX}]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: ENTITY-MIB
Object name: entPhysicalSerialNum','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fa0ce17966414937ba22b2a0891ca372','{#ENT_NAME}: HARDWARE SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34091','20','1.3.6.1.4.1.9.9.13.1.4.1.3.{#SNMPINDEX}','10393','{#SNMPVALUE}: Fan status','sensor.fan.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'248','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonFanState','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','aa190606669d43d996bce9c76df97081','{#SNMPVALUE}: FAN STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34092','20','1.3.6.1.4.1.9.9.48.1.1.1.6.{#SNMPINDEX}','10393','{#SNMPVALUE}: Free memory','vm.memory.free[{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-MEMORY-POOL-MIB
Object name: ciscoMemoryPoolFree
Indicates the number of bytes from the memory pool that are currently unused on the managed device. Note that the sum of ciscoMemoryPoolUsed and ciscoMemoryPoolFree is the total amount of memory in the pool
Reference: http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15216-contiguous-memory.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','44769632224a48dcb4756260910ba785','{#SNMPVALUE}: FREE MEMORY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34093','20','1.3.6.1.4.1.9.9.48.1.1.1.5.{#SNMPINDEX}','10393','{#SNMPVALUE}: Used memory','vm.memory.used[{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-MEMORY-POOL-MIB
Object name: ciscoMemoryPoolUsed
Indicates the number of bytes from the memory pool that are currently in use by applications on the managed device.
Reference: http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15216-contiguous-memory.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0f037e9121254776a84158ce1090ac80','{#SNMPVALUE}: USED MEMORY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34094','15','','10393','{#SNMPVALUE}: Memory utilization','vm.memory.util[{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'last(//vm.memory.used[{#SNMPINDEX}])/(last(//vm.memory.free[{#SNMPINDEX}])+last(//vm.memory.used[{#SNMPINDEX}]))*100','','0','','','','','2',NULL,'Memory utilization in %','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','926ffaaf890240be8d3632fe60b17c93','{#SNMPVALUE}: MEMORY UTILIZATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34095','20','1.3.6.1.2.1.2.2.1.13.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Inbound packets discarded','net.if.in.discards[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The number of inbound packets which were chosen to be discarded
even though no errors had been detected to prevent their being deliverable to a higher-layer protocol.
One possible reason for discarding such a packet could be to free up buffer space.
Discontinuities in the value of this counter can occur at re-initialization of the management system,
and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','757501460bb14d65b14cab2249e0f7b6','INTERFACE {#IFNAME}({#IFALIAS}): INBOUND PACKETS DISCARDED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34096','20','1.3.6.1.2.1.2.2.1.14.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Inbound packets with errors','net.if.in.errors[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
For packet-oriented interfaces, the number of inbound packets that contained errors preventing them from being deliverable to a higher-layer protocol.  For character-oriented or fixed-length interfaces, the number of inbound transmission units that contained errors preventing them from being deliverable to a higher-layer protocol. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4880d42b5c034fbaa07b5ccb3e74a3ae','INTERFACE {#IFNAME}({#IFALIAS}): INBOUND PACKETS WITH ERRORS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34097','20','1.3.6.1.2.1.31.1.1.1.6.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Bits received','net.if.in[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The total number of octets received on the interface, including framing characters. This object is a 64-bit version of ifInOctets. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e5e3c7c9d2904b19a7e8f0fe39d881db','INTERFACE {#IFNAME}({#IFALIAS}): BITS RECEIVED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34098','20','1.3.6.1.2.1.2.2.1.19.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Outbound packets discarded','net.if.out.discards[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The number of outbound packets which were chosen to be discarded
even though no errors had been detected to prevent their being deliverable to a higher-layer protocol.
One possible reason for discarding such a packet could be to free up buffer space.
Discontinuities in the value of this counter can occur at re-initialization of the management system,
and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6d0a3f00c7494655b8c67d6f257be372','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS DISCARDED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34099','20','1.3.6.1.2.1.2.2.1.20.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Outbound packets with errors','net.if.out.errors[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
For packet-oriented interfaces, the number of outbound packets that contained errors preventing them from being deliverable to a higher-layer protocol.  For character-oriented or fixed-length interfaces, the number of outbound transmission units that contained errors preventing them from being deliverable to a higher-layer protocol. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ce74da47f48e426a9364f92f58d50693','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS WITH ERRORS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34100','20','1.3.6.1.2.1.31.1.1.1.10.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Bits sent','net.if.out[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The total number of octets transmitted out of the interface, including framing characters. This object is a 64-bit version of ifOutOctets.Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a5efeed06f5f45d18e58517fb39323e8','INTERFACE {#IFNAME}({#IFALIAS}): BITS SENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34101','20','1.3.6.1.2.1.31.1.1.1.15.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Speed','net.if.speed[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
An estimate of the interface''s current bandwidth in units of 1,000,000 bits per second. If this object reports a value of `n'' then the speed of the interface is somewhere in the range of `n-500,000'' to`n+499,999''.  For interfaces which do not vary in bandwidth or for those where no accurate estimation can be made, this object should contain the nominal bandwidth. For a sub-layer which has no concept of bandwidth, this object should be zero.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','bc137542c8e14308bec44ac90469e8d0','INTERFACE {#IFNAME}({#IFALIAS}): SPEED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34102','20','1.3.6.1.2.1.2.2.1.8.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Operational status','net.if.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'250','','','0','','','','','2',NULL,'MIB: IF-MIB
The current operational state of the interface.
- The testing(3) state indicates that no operational packet scan be passed
- If ifAdminStatus is down(2) then ifOperStatus should be down(2)
- If ifAdminStatus is changed to up(1) then ifOperStatus should change to up(1) if the interface is ready to transmit and receive network traffic
- It should change todormant(5) if the interface is waiting for external actions (such as a serial line waiting for an incoming connection)
- It should remain in the down(2) state if and only if there is a fault that prevents it from going to the up(1) state
- It should remain in the notPresent(6) state if the interface has missing(typically, hardware) components.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f13cc69469844cbdad4f2eac0e7f045e','INTERFACE {#IFNAME}({#IFALIAS}): OPERATIONAL STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34103','20','1.3.6.1.2.1.2.2.1.3.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Interface type','net.if.type[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'251','','','0','','','','','2',NULL,'MIB: IF-MIB
The type of interface.
Additional values for ifType are assigned by the Internet Assigned Numbers Authority (IANA),
through updating the syntax of the IANAifType textual convention.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7bf551e444994cdaa08f208c10b89860','INTERFACE {#IFNAME}({#IFALIAS}): INTERFACE TYPE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34104','20','1.3.6.1.2.1.10.7.2.1.19.{#SNMPINDEX}','10393','Interface {#IFNAME}({#IFALIAS}): Duplex status','net.if.duplex[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'249','','','0','','','','','2',NULL,'MIB: EtherLike-MIB
Object name: dot3StatsDuplexStatus
The current mode of operation of the MAC
entity.  ''unknown'' indicates that the current
duplex mode could not be determined.

Management control of the duplex mode is
accomplished through the MAU MIB.  When
an interface does not support autonegotiation,
or when autonegotiation is not enabled, the
duplex mode is controlled using
ifMauDefaultType.  When autonegotiation is
supported and enabled, duplex mode is controlled
using ifMauAutoNegAdvertisedBits.  In either
case, the currently operating duplex mode is
reflected both in this object and in ifMauType.

Note that this object provides redundant
information with ifMauType.  Normally, redundant
objects are discouraged.  However, in this
instance, it allows a management application to
determine the duplex status of an interface
without having to know every possible value of
ifMauType.  This was felt to be sufficiently
valuable to justify the redundancy.
Reference: [IEEE 802.3 Std.], 30.3.1.1.32,aDuplexStatus.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3a3836aa72914f14b1ee8d48be3b2bd1','INTERFACE {#IFNAME}({#IFALIAS}): DUPLEX STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34105','20','1.3.6.1.4.1.9.9.13.1.5.1.3.{#SNMPINDEX}','10393','{#SNMPVALUE}: Power supply status','sensor.psu.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'248','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonSupplyState','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6ebc2645c84c4eb3acecaae528501cc2','{#SNMPVALUE}: POWER SUPPLY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34106','20','1.3.6.1.4.1.9.9.13.1.3.1.6.{#SNMPINDEX}','10393','{#SNMPVALUE}: Temperature status','sensor.temp.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'248','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonTemperatureState
The current state of the test point being instrumented.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b60cf661f8c949c4860cea6d0c39e87b','{#SNMPVALUE}: TEMPERATURE STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34107','20','1.3.6.1.4.1.9.9.13.1.3.1.3.{#SNMPINDEX}','10393','{#SNMPVALUE}: Temperature','sensor.temp.value[{#SNMPINDEX}]','1m','7d','365d','0','0','','°C','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonTemperatureValue
The current measurement of the test point being instrumented.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','957a69769a7d4d27930d82feb359b3d5','{#SNMPVALUE}: TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34108','3','','10394','ICMP ping','icmpping','1m','7d','365d','0','3','','','','',NULL,'258','','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5d096334d7e2455797c9a5a46fecfaec','ICMP PING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34109','3','','10394','ICMP loss','icmppingloss','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a88b7bcaa2174a76b09031993ee48fb4','ICMP LOSS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34110','3','','10394','ICMP response time','icmppingsec','1m','7d','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','906ca6fa0cf64000bac2efbc0f5dc7f9','ICMP RESPONSE TIME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34111','17','','10394','SNMP traps (fallback)','snmptrap.fallback','1m','7d','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'Item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','bc9c48b56cc6405c8256566d4768903a','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34112','20','1.3.6.1.2.1.1.4.0','10394','System contact details','system.contact','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed node, together with information on how to contact this person.  If no contact information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','19896943dda74f798241c176b1f4fc4f','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34113','20','1.3.6.1.2.1.1.1.0','10394','System description','system.descr','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c4bd78d5e1f442128eddcdf4ea22d4b3','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34114','20','1.3.6.1.2.1.47.1.1.1.1.13.1','10394','Hardware model name','system.hw.model','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: ENTITY-MIB','29','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','58642d7727964ba48f41bc33cfb6ef37','HARDWARE MODEL NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34115','20','1.3.6.1.2.1.47.1.1.1.1.11.1','10394','Hardware serial number','system.hw.serialnumber','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: ENTITY-MIB','8','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7fa7b4e4803e4eed932c176afed56cd5','HARDWARE SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34116','20','1.3.6.1.2.1.1.6.0','10394','System location','system.location','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet, 3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','213f54a3c23c40aa8693169efd8c0d82','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34117','20','1.3.6.1.2.1.1.5.0','10394','System name','system.name','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
An administratively-assigned name for this managed node.By convention, this is the node''s fully-qualified domain name.  If the name is unknown, the value is the zero-length string.','3','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7e325f94720f4b29ad83a741a3735fa1','SYSTEM NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34118','20','1.3.6.1.2.1.1.2.0','10394','System object ID','system.objectid','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management subsystem contained in the entity.  This value is allocated within the SMI enterprises subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1 to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2fce50826a7d498abe4ca628021fb9ac','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34119','20','1.3.6.1.2.1.1.1.0','10394','Operating system','system.sw.os','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB','5','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0d55299054304e658dc036f234727c73','OPERATING SYSTEM');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34120','20','1.3.6.1.2.1.1.3.0','10394','Uptime (network)','system.net.uptime','1m','7d','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d33f3f14dfff49d88269706ab464e2b9','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34121','5','','10394','SNMP agent availability','zabbix[host,snmp,available]','1m','7d','365d','0','3','','','','',NULL,'259','','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','82c87e2ade594f68abc4861e4d328a16','SNMP AGENT AVAILABILITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34122','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.109.1.1.1.1.5]','10394','CPU discovery','cpu.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'If your IOS device has several CPUs, you must use CISCO-PROCESS-MIB and its object cpmCPUTotal5minRev from the table called cpmCPUTotalTable ,
indexed with cpmCPUTotalIndex .
This table allows CISCO-PROCESS-MIB to keep CPU statistics for different physical entities in the router,
like different CPU chips, group of CPUs, or CPUs in different modules/cards.
In case of a single CPU, cpmCPUTotalTable has only one entry.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f472cb3505b34f14b84bc1ce69f66b29','CPU DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34123','20','discovery[{#ENT_CLASS},1.3.6.1.2.1.47.1.1.1.1.5,{#ENT_NAME},1.3.6.1.2.1.47.1.1.1.1.7,{#ENT_SN},1.3.6.1.2.1.47.1.1.1.1.11]','10394','Entity Serial Numbers discovery','entity_sn.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7b40466007144e82ba7b6081d9d024ae','ENTITY SERIAL NUMBERS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34124','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.13.1.4.1.2]','10394','FAN discovery','fan.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The table of fan status maintained by the environmental monitor.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4972e929a2e84bc1bf37f8844aa640d2','FAN DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34125','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.48.1.1.1.2]','10394','Memory discovery','memory.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of ciscoMemoryPoolTable, a table of memory pool monitoring entries.
http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15216-contiguous-memory.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d5c08c7436a44b74b35c4dd5be5c308a','MEMORY DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34126','20','discovery[{#IFOPERSTATUS},1.3.6.1.2.1.2.2.1.8,{#IFADMINSTATUS},1.3.6.1.2.1.2.2.1.7,{#IFALIAS},1.3.6.1.2.1.31.1.1.1.18,{#IFNAME},1.3.6.1.2.1.31.1.1.1.1,{#IFDESCR},1.3.6.1.2.1.2.2.1.2,{#IFTYPE},1.3.6.1.2.1.2.2.1.3]','10394','Network interfaces discovery','net.if.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovering interfaces from IF-MIB.','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c0be105de4db4c0182833e6a7e0fcd01','NETWORK INTERFACES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34127','20','discovery[{#SNMPVALUE},1.3.6.1.2.1.10.7.2.1.19,{#IFOPERSTATUS},1.3.6.1.2.1.2.2.1.8,{#IFALIAS},1.3.6.1.2.1.31.1.1.1.18,{#IFNAME},1.3.6.1.2.1.31.1.1.1.1,{#IFDESCR},1.3.6.1.2.1.2.2.1.2]','10394','EtherLike discovery','net.if.duplex.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovering interfaces from IF-MIB and EtherLike-MIB. Interfaces with up(1) Operational Status are discovered.','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','15992a60957c4ef896ece23744da52f1','ETHERLIKE DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34128','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.13.1.5.1.2]','10394','PSU discovery','psu.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The table of power supply status maintained by the environmental monitor card.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d2658fe23d274233accf16090273118f','PSU DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34129','20','discovery[{#SNMPVALUE},1.3.6.1.4.1.9.9.13.1.3.1.2]','10394','Temperature discovery','temperature.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of ciscoEnvMonTemperatureTable (ciscoEnvMonTemperatureDescr), a table of ambient temperature status
maintained by the environmental monitor.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ab60f4a103254b2c87f260014ecd1a28','TEMPERATURE DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34130','20','1.3.6.1.4.1.9.9.109.1.1.1.1.8.{#SNMPINDEX}','10394','#{#SNMPINDEX}: CPU utilization','system.cpu.util[{#SNMPINDEX}]','5m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-PROCESS-MIB
Object name: cpmCPUTotal5minRev
The cpmCPUTotal5minRev MIB object provides a more accurate view of the performance of the router over time than the MIB objects cpmCPUTotal1minRev and cpmCPUTotal5secRev . These MIB objects are not accurate because they look at CPU at one minute and five second intervals, respectively. These MIBs enable you to monitor the trends and plan the capacity of your network. The recommended baseline rising threshold for cpmCPUTotal5minRev is 90 percent. Depending on the platform, some routers that run at 90 percent, for example, 2500s, can exhibit performance degradation versus a high-end router, for example, the 7500 series, which can operate fine.
Reference: http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15215-collect-cpu-util-snmp.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','71248adcae1247fb8fe96ff83505b72a','#{#SNMPINDEX}: CPU UTILIZATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34131','20','1.3.6.1.2.1.47.1.1.1.1.11.{#SNMPINDEX}','10394','{#ENT_NAME}: Hardware serial number','system.hw.serialnumber[{#SNMPINDEX}]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: ENTITY-MIB
Object name: entPhysicalSerialNum','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c08c86fa7d1a4f16b51a8212eb98826f','{#ENT_NAME}: HARDWARE SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34132','20','1.3.6.1.4.1.9.9.13.1.4.1.3.{#SNMPINDEX}','10394','{#SNMPVALUE}: Fan status','sensor.fan.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'254','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonFanState','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6bc5cda2b5fa487d8841f6f9d07899e3','{#SNMPVALUE}: FAN STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34133','20','1.3.6.1.4.1.9.9.48.1.1.1.6.{#SNMPINDEX}','10394','{#SNMPVALUE}: Free memory','vm.memory.free[{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-MEMORY-POOL-MIB
Object name: ciscoMemoryPoolFree
Indicates the number of bytes from the memory pool that are currently unused on the managed device. Note that the sum of ciscoMemoryPoolUsed and ciscoMemoryPoolFree is the total amount of memory in the pool
Reference: http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15216-contiguous-memory.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3520b5d6482145958337956cb29d5dad','{#SNMPVALUE}: FREE MEMORY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34134','20','1.3.6.1.4.1.9.9.48.1.1.1.5.{#SNMPINDEX}','10394','{#SNMPVALUE}: Used memory','vm.memory.used[{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-MEMORY-POOL-MIB
Object name: ciscoMemoryPoolUsed
Indicates the number of bytes from the memory pool that are currently in use by applications on the managed device.
Reference: http://www.cisco.com/c/en/us/support/docs/ip/simple-network-management-protocol-snmp/15216-contiguous-memory.html','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5317e1db040846728cf05f3b7fe5dcab','{#SNMPVALUE}: USED MEMORY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34135','15','','10394','{#SNMPVALUE}: Memory utilization','vm.memory.util[{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'last(//vm.memory.used[{#SNMPINDEX}])/(last(//vm.memory.free[{#SNMPINDEX}])+last(//vm.memory.used[{#SNMPINDEX}]))*100','','0','','','','','2',NULL,'Memory utilization in %','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9120f609d03f44c68c5c34177745422c','{#SNMPVALUE}: MEMORY UTILIZATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34136','20','1.3.6.1.2.1.2.2.1.13.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Inbound packets discarded','net.if.in.discards[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The number of inbound packets which were chosen to be discarded
even though no errors had been detected to prevent their being deliverable to a higher-layer protocol.
One possible reason for discarding such a packet could be to free up buffer space.
Discontinuities in the value of this counter can occur at re-initialization of the management system,
and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','06f850ef11f24e79be813a8b79e25d91','INTERFACE {#IFNAME}({#IFALIAS}): INBOUND PACKETS DISCARDED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34137','20','1.3.6.1.2.1.2.2.1.14.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Inbound packets with errors','net.if.in.errors[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
For packet-oriented interfaces, the number of inbound packets that contained errors preventing them from being deliverable to a higher-layer protocol.  For character-oriented or fixed-length interfaces, the number of inbound transmission units that contained errors preventing them from being deliverable to a higher-layer protocol. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','216cd11617ce4fcb9551cbada0189919','INTERFACE {#IFNAME}({#IFALIAS}): INBOUND PACKETS WITH ERRORS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34138','20','1.3.6.1.2.1.31.1.1.1.6.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Bits received','net.if.in[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The total number of octets received on the interface, including framing characters. This object is a 64-bit version of ifInOctets. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9dfdb09ca395486b9b71f1e3d74b8f5a','INTERFACE {#IFNAME}({#IFALIAS}): BITS RECEIVED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34139','20','1.3.6.1.2.1.2.2.1.19.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Outbound packets discarded','net.if.out.discards[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The number of outbound packets which were chosen to be discarded
even though no errors had been detected to prevent their being deliverable to a higher-layer protocol.
One possible reason for discarding such a packet could be to free up buffer space.
Discontinuities in the value of this counter can occur at re-initialization of the management system,
and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','69fffa684b344774877ccb05e80fa0ab','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS DISCARDED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34140','20','1.3.6.1.2.1.2.2.1.20.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Outbound packets with errors','net.if.out.errors[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
For packet-oriented interfaces, the number of outbound packets that contained errors preventing them from being deliverable to a higher-layer protocol.  For character-oriented or fixed-length interfaces, the number of outbound transmission units that contained errors preventing them from being deliverable to a higher-layer protocol. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ce6a12b2553d456b87738efeb43ca849','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS WITH ERRORS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34141','20','1.3.6.1.2.1.31.1.1.1.10.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Bits sent','net.if.out[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The total number of octets transmitted out of the interface, including framing characters. This object is a 64-bit version of ifOutOctets.Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','eee4285b410f470f82e05c8f0cbc97b5','INTERFACE {#IFNAME}({#IFALIAS}): BITS SENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34142','20','1.3.6.1.2.1.31.1.1.1.15.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Speed','net.if.speed[{#SNMPINDEX}]','1m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
An estimate of the interface''s current bandwidth in units of 1,000,000 bits per second. If this object reports a value of `n'' then the speed of the interface is somewhere in the range of `n-500,000'' to`n+499,999''.  For interfaces which do not vary in bandwidth or for those where no accurate estimation can be made, this object should contain the nominal bandwidth. For a sub-layer which has no concept of bandwidth, this object should be zero.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b95c3c8730434b58a1a03c661c767901','INTERFACE {#IFNAME}({#IFALIAS}): SPEED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34143','20','1.3.6.1.2.1.2.2.1.8.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Operational status','net.if.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'256','','','0','','','','','2',NULL,'MIB: IF-MIB
The current operational state of the interface.
- The testing(3) state indicates that no operational packet scan be passed
- If ifAdminStatus is down(2) then ifOperStatus should be down(2)
- If ifAdminStatus is changed to up(1) then ifOperStatus should change to up(1) if the interface is ready to transmit and receive network traffic
- It should change todormant(5) if the interface is waiting for external actions (such as a serial line waiting for an incoming connection)
- It should remain in the down(2) state if and only if there is a fault that prevents it from going to the up(1) state
- It should remain in the notPresent(6) state if the interface has missing(typically, hardware) components.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','28cb37005e6c46eaa636b5de0b7b5c8d','INTERFACE {#IFNAME}({#IFALIAS}): OPERATIONAL STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34144','20','1.3.6.1.2.1.2.2.1.3.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Interface type','net.if.type[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'257','','','0','','','','','2',NULL,'MIB: IF-MIB
The type of interface.
Additional values for ifType are assigned by the Internet Assigned Numbers Authority (IANA),
through updating the syntax of the IANAifType textual convention.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','73d4de02c2e84a75acd66e33d98f6180','INTERFACE {#IFNAME}({#IFALIAS}): INTERFACE TYPE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34145','20','1.3.6.1.2.1.10.7.2.1.19.{#SNMPINDEX}','10394','Interface {#IFNAME}({#IFALIAS}): Duplex status','net.if.duplex[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'255','','','0','','','','','2',NULL,'MIB: EtherLike-MIB
Object name: dot3StatsDuplexStatus
The current mode of operation of the MAC
entity.  ''unknown'' indicates that the current
duplex mode could not be determined.

Management control of the duplex mode is
accomplished through the MAU MIB.  When
an interface does not support autonegotiation,
or when autonegotiation is not enabled, the
duplex mode is controlled using
ifMauDefaultType.  When autonegotiation is
supported and enabled, duplex mode is controlled
using ifMauAutoNegAdvertisedBits.  In either
case, the currently operating duplex mode is
reflected both in this object and in ifMauType.

Note that this object provides redundant
information with ifMauType.  Normally, redundant
objects are discouraged.  However, in this
instance, it allows a management application to
determine the duplex status of an interface
without having to know every possible value of
ifMauType.  This was felt to be sufficiently
valuable to justify the redundancy.
Reference: [IEEE 802.3 Std.], 30.3.1.1.32,aDuplexStatus.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','530a9cfa68024c1e8ad6573573c8f2b7','INTERFACE {#IFNAME}({#IFALIAS}): DUPLEX STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34146','20','1.3.6.1.4.1.9.9.13.1.5.1.3.{#SNMPINDEX}','10394','{#SNMPVALUE}: Power supply status','sensor.psu.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'254','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonSupplyState','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b87fda0166dc4baa9c24124dae6cea5c','{#SNMPVALUE}: POWER SUPPLY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34147','20','1.3.6.1.4.1.9.9.13.1.3.1.6.{#SNMPINDEX}','10394','{#SNMPVALUE}: Temperature status','sensor.temp.status[{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'254','','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonTemperatureState
The current state of the test point being instrumented.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2b2423e625914a4f89b16faaed832bae','{#SNMPVALUE}: TEMPERATURE STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34148','20','1.3.6.1.4.1.9.9.13.1.3.1.3.{#SNMPINDEX}','10394','{#SNMPVALUE}: Temperature','sensor.temp.value[{#SNMPINDEX}]','1m','7d','365d','0','0','','°C','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: CISCO-ENVMON-MIB
Object name: ciscoEnvMonTemperatureValue
The current measurement of the test point being instrumented.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','92864c59d4b34a979dc465824c3ef1b2','{#SNMPVALUE}: TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34149','3','','10251','ICMP ping','icmpping','1m','1w','365d','0','3','','','','',NULL,'262','','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','87480ce035a94f299c4cf4103eaaf066','ICMP PING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34150','3','','10251','ICMP loss','icmppingloss','1m','1w','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','50e85be3969447c58fcfeca5d9a1a9bb','ICMP LOSS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34151','3','','10251','ICMP response time','icmppingsec','1m','1w','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7567e999d75442379066babdc9b50894','ICMP RESPONSE TIME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34152','17','','10251','SNMP traps (fallback)','snmptrap.fallback','1m','2w','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'The item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0cb8aadeb5554583a65c3496cfed2c1b','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34153','20','1.3.6.1.2.1.1.4.0','10251','System contact details','system.contact[sysContact.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed node, together with information on how to contact this person.  If no contact information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f62a8b653c3d44d09864a4a4c910aeb1','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34154','20','discovery[{#CPU.UTIL},1.3.6.1.2.1.25.3.3.1.2]','10251','CPU utilization','system.cpu.util','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: HOST-RESOURCES-MIB
The average, over the last minute, of the percentage of time that processors was not idle.
Implementations may approximate this one minute smoothing period if necessary.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c33470549bda45e88ecb8ded7d0b5e87','CPU UTILIZATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34155','20','1.3.6.1.2.1.1.1.0','10251','System description','system.descr[sysDescr.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','64c4f3e890ec4c29be07ba2d06345534','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34156','20','1.3.6.1.2.1.1.6.0','10251','System location','system.location[sysLocation.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet, 3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e0d2149e1a114f3a971c324673beae2f','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34157','20','1.3.6.1.2.1.1.5.0','10251','System name','system.name','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
An administratively-assigned name for this managed node.By convention, this is the node''s fully-qualified domain name.  If the name is unknown, the value is the zero-length string.','3','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f63d1f71a97e45b0ab5716299ef298ea','SYSTEM NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34158','20','1.3.6.1.2.1.1.2.0','10251','System object ID','system.objectid[sysObjectID.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management subsystem contained in the entity.  This value is allocated within the SMI enterprises subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1 to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f1535f45138b472c945e231a9beb9cc5','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34159','20','1.3.6.1.2.1.1.3.0','10251','Uptime (network)','system.net.uptime[sysUpTime.0]','30s','2w','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d7f06d23f6b14677b5183f2cc94fc10d','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34160','5','','10251','SNMP agent availability','zabbix[host,snmp,available]','1m','7d','365d','0','3','','','','',NULL,'263','','','0','','','','','0',NULL,'Availability of SNMP checks on the host. The value of this item corresponds to availability icons in the host list.
Possible value:
0 - not available
1 - available
2 - unknown','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','aba117057e824b6789fca847cae9e0fc','SNMP AGENT AVAILABILITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34161','20','discovery[{#IFOPERSTATUS},1.3.6.1.2.1.2.2.1.8,{#IFADMINSTATUS},1.3.6.1.2.1.2.2.1.7,{#IFALIAS},1.3.6.1.2.1.31.1.1.1.18,{#IFNAME},1.3.6.1.2.1.31.1.1.1.1,{#IFDESCR},1.3.6.1.2.1.2.2.1.2,{#IFTYPE},1.3.6.1.2.1.2.2.1.3]','10251','Network interfaces discovery','net.if.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovering interfaces from IF-MIB.','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9e0d4ed074214f22bbbc9c8a5e3b9d0d','NETWORK INTERFACES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34162','20','discovery[{#FSNAME},1.3.6.1.2.1.25.2.3.1.3,{#FSTYPE},1.3.6.1.2.1.25.2.3.1.2,{#ALLOC_UNITS},1.3.6.1.2.1.25.2.3.1.4]','10251','Storage discovery','vfs.fs.discovery[snmp]','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'HOST-RESOURCES-MIB::hrStorage discovery with storage filter.','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f4c83472c88b419da104e4c5a35d6fc9','STORAGE DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34163','20','discovery[{#MEMNAME},1.3.6.1.2.1.25.2.3.1.3,{#MEMTYPE},1.3.6.1.2.1.25.2.3.1.2,{#ALLOC_UNITS},1.3.6.1.2.1.25.2.3.1.4]','10251','Memory discovery','vm.memory.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'HOST-RESOURCES-MIB::hrStorage discovery with memory filter','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','32a20a1f65d64db3bf17d6d405321253','MEMORY DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34164','20','1.3.6.1.2.1.2.2.1.13.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Inbound packets discarded','net.if.in.discards[ifInDiscards.{#SNMPINDEX}]','3m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The number of inbound packets which were chosen to be discarded
even though no errors had been detected to prevent their being deliverable to a higher-layer protocol.
One possible reason for discarding such a packet could be to free up buffer space.
Discontinuities in the value of this counter can occur at re-initialization of the management system,
and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','8f6e736b5c9c48a68e16122d592534b2','INTERFACE {#IFNAME}({#IFALIAS}): INBOUND PACKETS DISCARDED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34165','20','1.3.6.1.2.1.2.2.1.14.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Inbound packets with errors','net.if.in.errors[ifInErrors.{#SNMPINDEX}]','3m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
For packet-oriented interfaces, the number of inbound packets that contained errors preventing them from being deliverable to a higher-layer protocol.  For character-oriented or fixed-length interfaces, the number of inbound transmission units that contained errors preventing them from being deliverable to a higher-layer protocol. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c625b20266a04a1ba0421b4a64629dcc','INTERFACE {#IFNAME}({#IFALIAS}): INBOUND PACKETS WITH ERRORS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34166','20','1.3.6.1.2.1.31.1.1.1.6.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Bits received','net.if.in[ifHCInOctets.{#SNMPINDEX}]','3m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The total number of octets received on the interface, including framing characters. This object is a 64-bit version of ifInOctets. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','262f5aa5582441ecb93fd7df6a59a76d','INTERFACE {#IFNAME}({#IFALIAS}): BITS RECEIVED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34167','20','1.3.6.1.2.1.2.2.1.19.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Outbound packets discarded','net.if.out.discards[ifOutDiscards.{#SNMPINDEX}]','3m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The number of outbound packets which were chosen to be discarded
even though no errors had been detected to prevent their being deliverable to a higher-layer protocol.
One possible reason for discarding such a packet could be to free up buffer space.
Discontinuities in the value of this counter can occur at re-initialization of the management system,
and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b7c510be904e4d06830ae13a16bc9668','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS DISCARDED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34168','20','1.3.6.1.2.1.2.2.1.20.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Outbound packets with errors','net.if.out.errors[ifOutErrors.{#SNMPINDEX}]','3m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
For packet-oriented interfaces, the number of outbound packets that contained errors preventing them from being deliverable to a higher-layer protocol.  For character-oriented or fixed-length interfaces, the number of outbound transmission units that contained errors preventing them from being deliverable to a higher-layer protocol. Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','67b4b6520bbd45fd96d78a5942b54c09','INTERFACE {#IFNAME}({#IFALIAS}): OUTBOUND PACKETS WITH ERRORS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34169','20','1.3.6.1.2.1.31.1.1.1.10.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Bits sent','net.if.out[ifHCOutOctets.{#SNMPINDEX}]','3m','7d','365d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
The total number of octets transmitted out of the interface, including framing characters. This object is a 64-bit version of ifOutOctets.Discontinuities in the value of this counter can occur at re-initialization of the management system, and at other times as indicated by the value of ifCounterDiscontinuityTime.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','8e149281afb742758a00b699a281a584','INTERFACE {#IFNAME}({#IFALIAS}): BITS SENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34170','20','1.3.6.1.2.1.31.1.1.1.15.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Speed','net.if.speed[ifHighSpeed.{#SNMPINDEX}]','5m','7d','0d','0','3','','bps','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: IF-MIB
An estimate of the interface''s current bandwidth in units of 1,000,000 bits per second. If this object reports a value of `n'' then the speed of the interface is somewhere in the range of `n-500,000'' to`n+499,999''.  For interfaces which do not vary in bandwidth or for those where no accurate estimation can be made, this object should contain the nominal bandwidth. For a sub-layer which has no concept of bandwidth, this object should be zero.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ddbde55ce98f465a8973d60b1ecb0f8c','INTERFACE {#IFNAME}({#IFALIAS}): SPEED');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34171','20','1.3.6.1.2.1.2.2.1.8.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Operational status','net.if.status[ifOperStatus.{#SNMPINDEX}]','1m','7d','0','0','3','','','','',NULL,'260','','','0','','','','','2',NULL,'MIB: IF-MIB
The current operational state of the interface.
- The testing(3) state indicates that no operational packet scan be passed
- If ifAdminStatus is down(2) then ifOperStatus should be down(2)
- If ifAdminStatus is changed to up(1) then ifOperStatus should change to up(1) if the interface is ready to transmit and receive network traffic
- It should change todormant(5) if the interface is waiting for external actions (such as a serial line waiting for an incoming connection)
- It should remain in the down(2) state if and only if there is a fault that prevents it from going to the up(1) state
- It should remain in the notPresent(6) state if the interface has missing(typically, hardware) components.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6a1429de015640768d2cdd2adc4b09d7','INTERFACE {#IFNAME}({#IFALIAS}): OPERATIONAL STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34172','20','1.3.6.1.2.1.2.2.1.3.{#SNMPINDEX}','10251','Interface {#IFNAME}({#IFALIAS}): Interface type','net.if.type[ifType.{#SNMPINDEX}]','1h','7d','0d','0','3','','','','',NULL,'261','','','0','','','','','2',NULL,'MIB: IF-MIB
The type of interface.
Additional values for ifType are assigned by the Internet Assigned Numbers Authority (IANA),
through updating the syntax of the IANAifType textual convention.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7ecba23625b64d94873b938ebbce500b','INTERFACE {#IFNAME}({#IFALIAS}): INTERFACE TYPE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34173','15','','10251','{#FSNAME}: Space utilization','vfs.fs.pused[storageUsedPercentage.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'(last(//vfs.fs.used[hrStorageUsed.{#SNMPINDEX}])/last(//vfs.fs.total[hrStorageSize.{#SNMPINDEX}]))*100','','0','','','','','2',NULL,'Space utilization in % for {#FSNAME}','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','84e47981247243bd888a870700da8be3','{#FSNAME}: SPACE UTILIZATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34174','20','1.3.6.1.2.1.25.2.3.1.5.{#SNMPINDEX}','10251','{#FSNAME}: Total space','vfs.fs.total[hrStorageSize.{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: HOST-RESOURCES-MIB
The size of the storage represented by this entry, in units of hrStorageAllocationUnits.
This object is writable to allow remote configuration of the size of the storage area in those cases where such an operation makes sense and is possible on the underlying system.
For example, the amount of main storage allocated to a buffer pool might be modified or the amount of disk space allocated to virtual storage might be modified.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1a743f5b617f4800b5b2b9672f34693c','{#FSNAME}: TOTAL SPACE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34175','20','1.3.6.1.2.1.25.2.3.1.6.{#SNMPINDEX}','10251','{#FSNAME}: Used space','vfs.fs.used[hrStorageUsed.{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: HOST-RESOURCES-MIB
The amount of the storage represented by this entry that is allocated, in units of hrStorageAllocationUnits.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','82fadd771c3040c9ba001a9a40a83163','{#FSNAME}: USED SPACE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34176','20','1.3.6.1.2.1.25.2.3.1.5.{#SNMPINDEX}','10251','{#MEMNAME}: Total memory','vm.memory.total[hrStorageSize.{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: HOST-RESOURCES-MIB
The size of the storage represented by this entry, in units of hrStorageAllocationUnits.
This object is writable to allow remote configuration of the size of the storage area in those cases where such an operation makes sense and is possible on the underlying system.
For example, the amount of main memory allocated to a buffer pool might be modified or the amount of disk space allocated to virtual memory might be modified.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','70918ede8bff4f76be467a806a015b21','{#MEMNAME}: TOTAL MEMORY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34177','20','1.3.6.1.2.1.25.2.3.1.6.{#SNMPINDEX}','10251','{#MEMNAME}: Used memory','vm.memory.used[hrStorageUsed.{#SNMPINDEX}]','1m','7d','365d','0','3','','B','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: HOST-RESOURCES-MIB
The amount of the storage represented by this entry that is allocated, in units of hrStorageAllocationUnits.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e661062e7fcb45968ca1e9a1306f4848','{#MEMNAME}: USED MEMORY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34178','15','','10251','{#MEMNAME}: Memory utilization','vm.memory.util[memoryUsedPercentage.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'last(//vm.memory.used[hrStorageUsed.{#SNMPINDEX}])/last(//vm.memory.total[hrStorageSize.{#SNMPINDEX}])*100','','0','','','','','2',NULL,'Memory utilization in %.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','cedea4befd6a47b8983eff5dee9feed9','{#MEMNAME}: MEMORY UTILIZATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34180','20','1.3.6.1.4.1.318.1.1.1.4.3.3.0','10395','Output load','output.load[upsHighPrecOutputLoad]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current UPS load expressed as percentage
of rated capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c17c7fd7e6504592869dc14c4a002254','OUTPUT LOAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34181','20','1.3.6.1.2.1.1.3.0','10395','Uptime (network)','system.net.uptime[sysUpTime.0]','30s','2w','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management
portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','701fa778bc03444aad94343d0dbe048e','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34182','20','1.3.6.1.4.1.318.1.1.1.1.2.3.0','10395','Serial number','system.sn[upsAdvIdentSerialNumber]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
An 8-character string identifying the serial number of
 the UPS internal microprocessor.  This number is set at
 the factory.  NOTE: This number does NOT correspond to
 the serial number on the rear of the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1df309508ac9433397f88120b2895451','SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34183','20','1.3.6.1.2.1.1.2.0','10395','System object ID','system.objectid[sysObjectID.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management
subsystem contained in the entity.  This value is allocated within the SMI enterprises
subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what
kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was
assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1
to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6780faad9fc9492f9f92915db5161e43','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34185','20','1.3.6.1.4.1.318.1.1.1.1.1.1.0','10395','Model','system.model[upsBasicIdentModel]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS model name (e.g. ''APC Smart-UPS 600'').','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6030dbee3cc24dbeb15e4b802e89cbc8','MODEL');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34186','20','1.3.6.1.2.1.1.6.0','10395','System location','system.location[sysLocation.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet,
3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','445d7a843340424ab7c09ab001d5865c','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34187','20','1.3.6.1.2.1.1.1.0','10395','System description','system.descr[sysDescr.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ed42f6f2d8c24176b53f38e0a857a129','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34188','20','1.3.6.1.2.1.1.4.0','10395','System contact details','system.contact[sysContact.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed
node, together with information on how to contact this person.  If no contact
information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','299e4e11e0374888877e1dc386409726','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34189','17','','10395','SNMP traps (fallback)','snmptrap.fallback','1m','2w','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'The item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2c52ba1a964a40e1b4a75582ee6ad43b','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34190','20','1.3.6.1.4.1.318.1.1.1.4.3.1.0','10395','Output voltage','output.voltage[upsHighPrecOutputVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The output voltage of the UPS system in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','37d7eda5664c4ae2b4a126c60a8eb40b','OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34191','20','1.3.6.1.4.1.318.1.1.1.4.1.1.0','10395','Output status','output.status[upsBasicOutputStatus]','1m','7d','365d','0','3','','','','',NULL,'315','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current state of the UPS. If the UPS is unable to
 determine the state of the UPS this variable is set
 to unknown(1).
During self-test most UPSes report onBattery(3) but
 some that support it will report onBatteryTest(15).
 To determine self-test status across all UPSes, refer
 to the upsBasicStateOutputState OID.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0ae99a18a5c24fb0b812353d25459e1f','OUTPUT STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34192','20','1.3.6.1.4.1.318.1.1.1.4.3.4.0','10395','Output current','output.current[upsHighPrecOutputCurrent]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current in amperes drawn by the load on the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a332c87a948045beae13f74984245b86','OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34193','20','1.3.6.1.4.1.318.1.1.1.2.2.5.0','10395','External battery packs count','battery.external_packs_count[upsAdvBatteryNumOfBattPacks]','1h','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS. If
 the UPS does not use smart cells then the agent reports
 ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','390e33a7623d41d2a8a67752c6d5c733','EXTERNAL BATTERY PACKS COUNT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34194','20','1.3.6.1.4.1.318.1.1.1.3.3.1.0','10395','Input voltage','input.voltage[upsHighPrecInputLineVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current utility line voltage in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','de84a2fbbb464023a7b73e01895a9e9d','INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34195','20','1.3.6.1.4.1.318.1.1.1.3.3.4.0','10395','Input frequency','input.frequency[upsHighPrecInputFrequency]','1m','7d','365d','0','0','','Hz','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current input frequency to the UPS system in Hz.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2c0b565f2b6a44a2a91cc61fd220f056','INPUT FREQUENCY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34196','20','1.3.6.1.4.1.318.1.1.1.3.2.5.0','10395','Input fail cause','input.fail[upsAdvInputLineFailCause]','1m','7d','365d','0','3','','','','',NULL,'266','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The reason for the occurrence of the last transfer to UPS
battery power.  The variable is set to:
- noTransfer(1) -- if there is no transfer yet.
- highLineVoltage(2) -- if the transfer to battery is caused
by an over voltage greater than the high transfer voltage.
- brownout(3) -- if the duration of the outage is greater than
five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- blackout(4) -- if the duration of the outage is greater than five
seconds and the line voltage is between 40% of the rated
output voltage and ground.
- smallMomentarySag(5) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- deepMomentarySag(6) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and ground.  The variable is set to
- smallMomentarySpike(7) -- if the line failure is caused by a
rate of change of input voltage less than ten volts per cycle.
- largeMomentarySpike(8) -- if the line failure is caused by
a rate of change of input voltage greater than ten volts per cycle.
- selfTest(9) -- if the UPS was commanded to do a self test.
- rateOfVoltageChange(10) -- if the failure is due to the rate of change of
the line voltage.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6ce40beab0b44248868652b0ed543afc','INPUT FAIL CAUSE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34200','20','1.3.6.1.4.1.318.1.1.1.2.3.4.0','10395','Battery voltage','battery.voltage[upsHighPrecBatteryActualVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The actual battery bus voltage in Volts.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b78d2e9160c74f328b8123ba2031d7bf','BATTERY VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34201','20','1.3.6.1.4.1.318.1.1.1.2.3.2.0','10395','Battery temperature','battery.temperature[upsHighPrecBatteryTemperature]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current internal UPS temperature in Celsius.
 Temperatures below zero read as 0.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7c35a9646eed4e4581edc51d42a9604c','BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34202','20','1.3.6.1.4.1.318.1.1.1.2.1.1.0','10395','Battery status','battery.status[upsBasicBatteryStatus]','1m','7d','365d','0','3','','','','',NULL,'267','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The status of the UPS batteries. A batteryLow(3) value
 indicates the UPS will be unable to sustain the current
 load, and its services will be lost if power is not restored.
 The amount of run time in reserve at the time of low battery
 can be configured by the upsAdvConfigLowBatteryRunTime.
 A batteryInFaultCondition(4)value indicates that a battery
 installed has an internal error condition.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f4106603e47e40548592d60a7b8b3148','BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34203','20','1.3.6.1.4.1.318.1.1.1.2.2.3.0','10395','Battery runtime remaining','battery.runtime_remaining[upsAdvBatteryRunTimeRemaining]','1m','7d','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS battery run time remaining before battery
 exhaustion.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f52a3e2ae08c4b2996249c5601b4098d','BATTERY RUNTIME REMAINING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34204','20','1.3.6.1.4.1.318.1.1.1.2.2.4.0','10395','Battery replace indicator','battery.replace_indicator[upsAdvBatteryReplaceIndicator]','1m','7d','365d','0','3','','','','',NULL,'265','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
Indicates whether the UPS batteries need replacement.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','eb74b3671b4d4335ad92bd3b027547b0','BATTERY REPLACE INDICATOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34205','20','1.3.6.1.4.1.318.1.1.1.2.1.3.0','10395','Battery last replace date','battery.last_replace_date[upsBasicBatteryLastReplaceDate]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The date when the UPS system''s batteries were last replaced
 in mm/dd/yy (or yyyy) format. For Smart-UPS models, this value
 is originally set at the factory. When the UPS batteries
 are replaced, this value should be reset by the administrator.
 For Symmetra PX 250/500 this OID is read-only and is configurable in the local display only.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3d69adaa88e64b8084d38c1482815bf2','BATTERY LAST REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34206','5','','10395','SNMP agent availability','zabbix[host,snmp,available]','1m','7d','365d','0','3','','','','',NULL,'269','','','0','','','','','0',NULL,'Availability of SNMP checks on the host. The value of this item corresponds to availability icons in the host list.
Possible value:
0 - not available
1 - available
2 - unknown','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ca3275f69f3c4e7c9c71108451c0b64f','SNMP AGENT AVAILABILITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34207','20','discovery[{#EXTERNAL_PACKS},1.3.6.1.4.1.318.1.1.1.2.2.6]','10395','External bad battery packs discovery','battery.packs.bad.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of the number of external defective battery packs.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','52345d2975214002bdd05a24e43484a8','EXTERNAL BAD BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34208','20','discovery[{#CARTRIDGE_STATUS},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7,{#BATTERY_PACK},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.1,{#CARTRIDGE_INDEX},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.2]','10395','External battery packs discovery','battery.packs.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f7eb1c82c6694e72b7d28ba4d71d8741','EXTERNAL BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34209','20','discovery[{#EXTERNAL_SENSOR1_NAME},1.3.6.1.4.1.318.1.1.25.1.2.1.3]','10395','External sensor port 1 discovery','external.sensor1.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','457169b3c43846739614a6ddc7155fda','EXTERNAL SENSOR PORT 1 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34210','20','discovery[{#EXTERNAL_SENSOR2_NAME},1.3.6.1.4.1.318.1.1.25.1.2.2.3]','10395','External sensor port 2 discovery','external.sensor2.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','06a853147fe646659d066fff34f67faa','EXTERNAL SENSOR PORT 2 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34211','20','discovery[{#PHASEINDEX},1.3.6.1.4.1.318.1.1.1.9.2.3.1.2.1.1]','10395','Input phases discovery','input.phases.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The input phase identifier. OID upsPhaseInputPhaseIndex.1.1','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','16e8b3b4d38040a7961b1de4c18a4ea9','INPUT PHASES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34212','20','1.3.6.1.4.1.318.1.1.1.2.2.6.0','10395','{#SNMPINDEX}: External battery packs bad','battery.external_packs_bad[upsAdvBatteryNumOfBadBattPacks.{#SNMPINDEX}]','15m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS that
are defective. If the UPS does not use smart cells then the
agent reports ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c4dccc96218448d696952f6ea5d1f24b','{#SNMPINDEX}: EXTERNAL BATTERY PACKS BAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34213','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.8.{#SNMPINDEX}','10395','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery estimated replace date','battery.estimated_replace_date[upsHighPrecBatteryPackCartridgeReplaceDate.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge estimated battery replace date.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a168ef9da6504b31a8234b272f1a1a80','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY ESTIMATED REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34214','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7.{#SNMPINDEX}','10395','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery pack cartridge health','battery.pack.cartridge_health[upsHighPrecBatteryPackCartridgeHealth.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge health.
  bit 0 Battery lifetime okay
  bit 1 Battery lifetime near end, order replacement cartridge
  bit 2 Battery lifetime exceeded, replace battery
  bit 3 Battery lifetime near end acknowledged, order replacement cartridge
  bit 4 Battery lifetime exceeded acknowledged, replace battery
  bit 5 Battery measured lifetime near end, order replacement cartridge
  bit 6 Battery measured lifetime near end acknowledged, order replacement cartridge','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fd71d1ceaf524aeaac38de5f63d101fd','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY PACK CARTRIDGE HEALTH');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34215','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.10.{#SNMPINDEX}','10395','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery status','battery.pack.status[upsHighPrecBatteryPackCartridgeStatus.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge status.
bit 0 Disconnected
bit 1 Overvoltage
bit 2 NeedsReplacement
bit 3 OvertemperatureCritical
bit 4 Charger
bit 5 TemperatureSensor
bit 6 BusSoftStart
bit 7 OvertemperatureWarning
bit 8 GeneralError
bit 9 Communication
bit 10 DisconnectedFrame
bit 11 FirmwareMismatch','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fa05e062413a4c1fba4d35e3006b91f4','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34216','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.5.{#SNMPINDEX}','10395','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery temperature','battery.temperature[upsHighPrecBatteryPackTemperature.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack temperature in Celsius.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','017347865030426e9dde74e9bcf38c76','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34217','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.4.{#SNMPINDEX}','10395','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Serial number','system.sn[upsHighPrecBatteryPackSerialNumber.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack serial number.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','354c1d6766d6453caeb382cf7ede7951','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34218','20','1.3.6.1.4.1.318.1.1.25.1.2.1.7.1.1','10395','{#EXTERNAL_SENSOR1_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ee017a632ee944fe9122e21fa7e7531f','{#EXTERNAL_SENSOR1_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34219','20','1.3.6.1.4.1.318.1.1.25.1.2.1.9.1.1','10395','{#EXTERNAL_SENSOR1_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.1.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'264','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0431cf0a54b449c9b77623b69629920f','{#EXTERNAL_SENSOR1_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34220','20','1.3.6.1.4.1.318.1.1.25.1.2.1.6.1.1','10395','{#EXTERNAL_SENSOR1_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6de4920e4e87418884a82ff8b40a46ab','{#EXTERNAL_SENSOR1_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34221','20','1.3.6.1.4.1.318.1.1.25.1.2.2.7.1.1','10395','{#EXTERNAL_SENSOR2_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3417b035a4f14ce3992e10029674de8e','{#EXTERNAL_SENSOR2_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34222','20','1.3.6.1.4.1.318.1.1.25.1.2.2.9.1.1','10395','{#EXTERNAL_SENSOR2_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.2.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'264','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d04af1687eb846d18b57af04ab1b594b','{#EXTERNAL_SENSOR2_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34223','20','1.3.6.1.4.1.318.1.1.25.1.2.2.6.1.1','10395','{#EXTERNAL_SENSOR2_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','bbf611aad1454b38ad39fa258239394a','{#EXTERNAL_SENSOR2_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34224','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.6.1.1.{#PHASEINDEX}','10395','{#PHASEINDEX}: Phase input current','phase.input.current[upsPhaseInputCurrent.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input current in 0.1 amperes, or -0.1 if it''s
 unsupported by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a1b8277cd1b248348263c233ab05fd4f','{#PHASEINDEX}: PHASE INPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34225','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.3.1.1.{#PHASEINDEX}','10395','{#PHASEINDEX}: Phase input voltage','phase.input.voltage[upsPhaseInputVoltage.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input voltage in VAC, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','40c05eaf739540979d11787a694cb8c9','{#PHASEINDEX}: PHASE INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34226','19','','10396','Get chassis','netapp.chassis.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/cluster/chassis?fields=id,state','','','200','1','0','','0','0','0','0','0','0','0','95d822159f2a4c4084ad36b18cd11a1d','GET CHASSIS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34227','15','','10396','Cluster latency, read','netapp.cluster.statistics.latency.read','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.cluster.statistics.latency_raw.read) - last(//netapp.cluster.statistics.latency_raw.read,#2)) /
( last(//netapp.cluster.statistics.iops_raw.read) - last(//netapp.cluster.statistics.iops_raw.read,#2) +
(last(//netapp.cluster.statistics.iops_raw.read) - last(//netapp.cluster.statistics.iops_raw.read,#2) = 0) ) * 0.001','','0','','','','','0',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric for read I/O operations.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4b89e603f9cf4b92a85293b1ad15c005','CLUSTER LATENCY, READ');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34228','19','','10396','Get SVMs','netapp.svms.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/svm/svms?fields=name,state,comment','','','200','1','0','','0','0','0','0','0','0','0','7a813b7cb05d497fbf77bf11b01757dd','GET SVMS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34229','19','','10396','Get FC ports','netapp.ports.fc.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/network/fc/ports?fields=name,node.name,description,enabled,fabric.switch_port,state','','','200','1','0','','0','0','0','0','0','0','0','2a6abfe87cc548bb81fcb217cde4f805','GET FC PORTS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34230','19','','10396','Get ethernet ports','netapp.ports.eth.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/network/ethernet/ports?fields=name,type,node.name,broadcast_domain.name,enabled,state,mtu,speed','','','200','1','0','','0','0','0','0','0','0','0','c677a3caf7a04710bc67b165b4152808','GET ETHERNET PORTS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34231','19','','10396','Get nodes','netapp.nodes.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/cluster/nodes?fields=*','','','200','1','0','','0','0','0','0','0','0','0','5c36efc545ba4dcbb0be84da5e8088cc','GET NODES');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34232','19','','10396','Get LUNs','netapp.luns.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/storage/luns?fields=name,svm.name,space.size,space.used,status.state,status.container_state','','','200','1','0','','0','0','0','0','0','0','0','c9b6ac2405af48c0899d1536662f752b','GET LUNS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34233','19','','10396','Get FRUs','netapp.frus.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/cluster/chassis?fields=id,frus.id,frus.state','','','200','1','0','','0','0','0','0','0','0','0','54163ca73a8c40188048ef5d89ec4927','GET FRUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34234','19','','10396','Get disks','netapp.disks.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/storage/disks?fields=state,node.name','','','200','1','0','','0','0','0','0','0','0','0','c9bf91e0f23c4961aed8ee5b32ff7767','GET DISKS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34235','19','','10396','Get cluster','netapp.cluster.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/cluster','','','200','1','0','','0','0','0','0','0','0','0','49490a886b5f4e5c9e8cc121a6ffd713','GET CLUSTER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34236','15','','10396','Cluster latency, write','netapp.cluster.statistics.latency.write','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.cluster.statistics.latency_raw.write) - last(//netapp.cluster.statistics.latency_raw.write,#2)) /
( last(//netapp.cluster.statistics.iops_raw.write) - last(//netapp.cluster.statistics.iops_raw.write,#2) +
(last(//netapp.cluster.statistics.iops_raw.write) - last(//netapp.cluster.statistics.iops_raw.write,#2) = 0) ) * 0.001','','0','','','','','0',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric for write I/O operations.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','543ba306d85e41c98d34dab39463dd87','CLUSTER LATENCY, WRITE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34237','15','','10396','Cluster latency, total','netapp.cluster.statistics.latency.total','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.cluster.statistics.latency_raw.total) - last(//netapp.cluster.statistics.latency_raw.total,#2)) /
( last(//netapp.cluster.statistics.iops_raw.total) - last(//netapp.cluster.statistics.iops_raw.total,#2) +
(last(//netapp.cluster.statistics.iops_raw.total) - last(//netapp.cluster.statistics.iops_raw.total,#2) = 0) ) * 0.001','','0','','','','','0',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric aggregated over all types of I/O operations.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2c953f67a7484e389d11ac5ef6b06c44','CLUSTER LATENCY, TOTAL');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34238','19','','10396','Get volumes','netapp.volumes.get','1m','0','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','0',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/storage/volumes?fields=name,comment,state,type,svm.name,space.size,space.available,space.used,statistics','','','200','1','0','','0','0','0','0','0','0','0','fa7fa8daaaa640d494af38614ba12c2e','GET VOLUMES');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34239','15','','10396','Cluster latency, other','netapp.cluster.statistics.latency.other','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.cluster.statistics.latency_raw.other) - last(//netapp.cluster.statistics.latency_raw.other,#2)) /
(last(//netapp.cluster.statistics.iops_raw.other) - last(//netapp.cluster.statistics.iops_raw.other,#2) +
(last(//netapp.cluster.statistics.iops_raw.other) - last(//netapp.cluster.statistics.iops_raw.other,#2) = 0) ) * 0.001','','0','','','','','0',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric for other I/O operations. Other I/O operations can be metadata operations, such as directory lookups and so on.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4bd4fe94e9a54fa2b8ab9bdf0475edff','CLUSTER LATENCY, OTHER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34260','19','','10396','Chassis discovery','netapp.chassis.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/cluster/chassis?fields=id','','','200','1','0','','0','0','0','0','0','0','0','c5265605c1b5440999b7c0dbff8ce328','CHASSIS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34261','19','','10396','Disks discovery','netapp.disks.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/storage/disks?fields=name,node.name','','','200','1','0','','0','0','0','0','0','0','0','e7c0955f88d342179b96f56e1f35afe2','DISKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34263','19','','10396','LUNs discovery','netapp.luns.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/storage/luns?fields=name,svm.name,space.size,space.used,status.state,status.container_state','','','200','1','0','','0','0','0','0','0','0','0','b75474be384f4d7fa0f625c4cebeef43','LUNS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34264','19','','10396','Nodes discovery','netapp.nodes.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/cluster/nodes?fields=name','','','200','1','0','','0','0','0','0','0','0','0','b914c4c37ba446eba7ecdc73a9692885','NODES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34265','19','','10396','Ethernet ports discovery','netapp.ports.ether.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/network/ethernet/ports?fields=name,state,node.name','','','200','1','0','','0','0','0','0','0','0','0','98ed5727ede8490b8479a2194b2c847a','ETHERNET PORTS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34266','19','','10396','FC ports discovery','netapp.ports.fc.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/network/fc/ports?fields=node.name,name,state','','','200','1','0','','0','0','0','0','0','0','0','bab3f935c2a04c89b0901f1c19d50558','FC PORTS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34267','19','','10396','SVMs discovery','netapp.svms.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/svm/svms?fields=name','','','200','1','0','','0','0','0','0','0','0','0','b2a5b50d7e3e4592ad9627ae85487554','SVMS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34268','19','','10396','Volumes discovery','netapp.volumes.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','1','{$USERNAME}','{$PASSWORD}','','','1',NULL,'','0','30d','0','',NULL,'{$HTTP.AGENT.TIMEOUT}','{$URL}/api/storage/volumes?fields=name','','','200','1','0','','0','0','0','0','0','0','0','3d2001596c2642e7a6ee09d3ac7effb3','VOLUMES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34269','15','','10396','{#VOLUMENAME}: Volume latency, other','netapp.volume.statistics.latency.other[{#VOLUMENAME}]','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.volume.statistics.latency_raw.other[{#VOLUMENAME}]) - last(//netapp.volume.statistics.latency_raw.other[{#VOLUMENAME}],#2)) /
( last(//netapp.volume.statistics.iops_raw.other[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.other[{#VOLUMENAME}],#2) +
(last(//netapp.volume.statistics.iops_raw.other[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.other[{#VOLUMENAME}],#2) = 0) ) * 0.001','','0','','','','','2',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric for other I/O operations. Other I/O operations can be metadata operations, such as directory lookups and so on.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fc21c2c1ff87454ea9fc59af4d0d4693','{#VOLUMENAME}: VOLUME LATENCY, OTHER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34270','15','','10396','{#VOLUMENAME}: Volume latency, read','netapp.volume.statistics.latency.read[{#VOLUMENAME}]','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.volume.statistics.latency_raw.read[{#VOLUMENAME}]) - last(//netapp.volume.statistics.latency_raw.read[{#VOLUMENAME}],#2)) /
( last(//netapp.volume.statistics.iops_raw.read[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.read[{#VOLUMENAME}],#2) +
(last(//netapp.volume.statistics.iops_raw.read[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.read[{#VOLUMENAME}],#2) = 0)) * 0.001','','0','','','','','2',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric for read I/O operations.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3e80e6c55bd0497f87d4f4e71f11f0aa','{#VOLUMENAME}: VOLUME LATENCY, READ');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34271','15','','10396','{#VOLUMENAME}: Volume latency, write','netapp.volume.statistics.latency.write[{#VOLUMENAME}]','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.volume.statistics.latency_raw.write[{#VOLUMENAME}]) - last(//netapp.volume.statistics.latency_raw.write[{#VOLUMENAME}],#2)) /
( last(//netapp.volume.statistics.iops_raw.write[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.write[{#VOLUMENAME}],#2) +
(last(//netapp.volume.statistics.iops_raw.write[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.write[{#VOLUMENAME}],#2) = 0) ) * 0.001','','0','','','','','2',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric for write I/O operations.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','eb2b3a3c4807415a8a88d11b19ae7fe6','{#VOLUMENAME}: VOLUME LATENCY, WRITE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34272','15','','10396','{#VOLUMENAME}: Volume latency, total','netapp.volume.statistics.latency.total[{#VOLUMENAME}]','1m','7d','365d','0','0','','!ms','','',NULL,NULL,'(last(//netapp.volume.statistics.latency_raw.total[{#VOLUMENAME}]) - last(//netapp.volume.statistics.latency_raw.total[{#VOLUMENAME}],#2)) /
( last(//netapp.volume.statistics.iops_raw.total[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.total[{#VOLUMENAME}],#2) +
(last(//netapp.volume.statistics.iops_raw.total[{#VOLUMENAME}]) - last(//netapp.volume.statistics.iops_raw.total[{#VOLUMENAME}],#2) = 0) ) * 0.001','','0','','','','','2',NULL,'The average latency per I/O operation in milliseconds observed at the storage object. Performance metric aggregated over all types of I/O operations.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ff804a090b064bfeb60183d7d7d2abe1','{#VOLUMENAME}: VOLUME LATENCY, TOTAL');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34316','5','','10047','Zabbix server: Utilization of report writer internal processes, in %','zabbix[process,report writer,avg,busy]','1m','1w','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'The average percentage of the time during which the report writer processes have been busy for the last minute.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9c74858428cb4578b8a9095140b64d52','ZABBIX SERVER: UTILIZATION OF REPORT WRITER INTERNAL PROCESSES, IN %');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34317','5','','10047','Zabbix server: Utilization of report manager internal processes, in %','zabbix[process,report manager,avg,busy]','1m','1w','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'The average percentage of the time during which the report manager processes have been busy for the last minute.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3db38f5d250741fd833aec23e09bc52e','ZABBIX SERVER: UTILIZATION OF REPORT MANAGER INTERNAL PROCESSES, IN %');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34322','11','','10327','MSSQL: Get job status','db.odbc.get[get_job_status,"{$MSSQL.DSN}"]','10m','0','0','0','4','','','','',NULL,NULL,'SELECT sj.name AS JobName
, sj.enabled AS Enabled
, sjs.last_run_outcome AS RunStatus
, sjs.last_outcome_message AS LastRunStatusMessage
, sjs.last_run_duration/10000*3600 + sjs.last_run_duration/100%100*60 + sjs.last_run_duration%100 AS RunDuration
, CASE sjs.last_run_date
    WHEN 0 THEN NULL
    ELSE msdb.dbo.agent_datetime(sjs.last_run_date,sjs.last_run_time)
    END AS LastRunDateTime
, sja.next_scheduled_run_date AS NextRunDateTime
FROM msdb..sysjobs AS sj
LEFT JOIN msdb..sysjobservers AS sjs ON sj.job_id = sjs.job_id
LEFT JOIN ( SELECT job.job_id,
    max(act.session_id) AS s_id,
    max(act.next_scheduled_run_date) AS next_scheduled_run_date
    FROM msdb..sysjobs AS job
    LEFT JOIN msdb..sysjobactivity AS act ON act.job_id = job.job_id
    GROUP BY job.job_id ) AS sja ON sja.job_id = sj.job_id
WHERE Enabled = 1','','0','{$MSSQL.USER}','{$MSSQL.PASSWORD}','','','0',NULL,'The item gets sql agent job status.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','cae1f9b034b04357b038212b04cac794','MSSQL: GET JOB STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34323','11','','10327','MSSQL: Get last backup','db.odbc.get[get_last_backup,"{$MSSQL.DSN}"]','10m','0','0','0','4','','','','',NULL,NULL,'SELECT bs.database_name as dbname,[type], DATEDIFF(SECOND, bs.backup_finish_date, getdate()) as timesincelastbackup, (DATEDIFF(SECOND, bs.backup_start_date, bs.backup_finish_date)) as duration
FROM msdb.dbo.backupset as bs WHERE bs.database_name not in (
SELECT
AGDatabases.database_name AS Databasename
FROM sys.dm_hadr_availability_group_states States
INNER JOIN master.sys.availability_groups Groups ON States.group_id = Groups.group_id
INNER JOIN sys.availability_databases_cluster AGDatabases ON Groups.group_id = AGDatabases.group_id
WHERE primary_replica != @@Servername OR primary_replica is NULL
)
GROUP BY bs.database_name, backup_finish_date, [type], backup_start_date
HAVING backup_finish_date = (SELECT MAX(backup_finish_date) from msdb.dbo.backupset WHERE database_name = bs.database_name AND bs.type = [type])
ORDER BY bs.database_name','','0','{$MSSQL.USER}','{$MSSQL.PASSWORD}','','','0',NULL,'The item gets information about backup processes.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9b106ca122fb4b75a761e80f4239f906','MSSQL: GET LAST BACKUP');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34324','11','','10327','Job discovery','db.odbc.discovery[jobname,"{$MSSQL.DSN}"]','1h','90d','0','0','4','','','','',NULL,NULL,'SELECT name AS jobname FROM msdb..sysjobs WHERE enabled = 1','','0','{$MSSQL.USER}','{$MSSQL.PASSWORD}','','','1',NULL,'Scanning jobs in DBMS.','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6d972c575a944d49badfc2e6a614f686','JOB DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34336','19','','10397','PD: Get instance metrics','pd.get_metrics','1m','0','0','0','4','','','','',NULL,NULL,'','','0','','','','','0',NULL,'Get TiDB PD instance metrics.','0','30d','0','',NULL,'3s','{$PD.URL}:{$PD.PORT}/metrics','','','200','1','0','','0','0','0','0','0','0','0','3a1fd879a08a445cbf438f3d68078111','PD: GET INSTANCE METRICS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34337','19','','10397','PD: Get instance status','pd.get_status','1m','0','0','0','4','','','','',NULL,NULL,'','','0','','','','','0',NULL,'Get TiDB PD instance status info.','0','30d','0','',NULL,'3s','{$PD.URL}:{$PD.PORT}/pd/api/v1/status','','','200','1','0','','0','0','0','0','0','0','0','7eb740eed4eb43a0a449e1c1436e582b','PD: GET INSTANCE STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34367','19','','10398','TiDB: Get instance status','tidb.get_status','1m','0','0','0','4','','','','',NULL,NULL,'','','0','','','','','0',NULL,'Get TiDB instance status info.','0','30d','0','',NULL,'3s','{$TIDB.URL}:{$TIDB.PORT}/status','','','200','1','0','','0','0','0','0','0','0','0','e95ebe1050b8404f8274e243203fdecc','TIDB: GET INSTANCE STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34368','19','','10398','TiDB: Get instance metrics','tidb.get_metrics','1m','0','0','0','4','','','','',NULL,NULL,'','','0','','','','','0',NULL,'Get TiDB instance metrics.','0','30d','0','',NULL,'3s','{$TIDB.URL}:{$TIDB.PORT}/metrics','','','200','1','0','','0','0','0','0','0','0','0','954f5e433a7c44128d7772b87d493270','TIDB: GET INSTANCE METRICS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34412','19','','10399','TiKV: Get instance metrics','tikv.get_metrics','1m','0','0','0','4','','','','',NULL,NULL,'','','0','','','','','0',NULL,'Get TiKV instance metrics.','0','30d','0','',NULL,'3s','{$TIKV.URL}:{$TIKV.PORT}/metrics','','','200','1','0','','0','0','0','0','0','0','0','418bcc8c0bc440468efe833bef02929d','TIKV: GET INSTANCE METRICS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34451','20','1.3.6.1.4.1.318.1.1.1.2.3.1.0','10400','Battery capacity','battery.capacity[upsHighPrecBatteryCapacity]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The remaining battery capacity expressed as
 percentage of full capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','70ebcb1dee674a60a1410895d60e8245','BATTERY CAPACITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34452','20','1.3.6.1.4.1.318.1.1.1.4.1.1.0','10400','Output status','output.status[upsBasicOutputStatus]','1m','7d','365d','0','3','','','','',NULL,'277','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current state of the UPS. If the UPS is unable to
 determine the state of the UPS this variable is set
 to unknown(1).
During self-test most UPSes report onBattery(3) but
 some that support it will report onBatteryTest(15).
 To determine self-test status across all UPSes, refer
 to the upsBasicStateOutputState OID.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','8a6c9b134ebc4fd19876cf5d50dfc17b','OUTPUT STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34453','20','1.3.6.1.2.1.1.3.0','10400','Uptime (network)','system.net.uptime[sysUpTime.0]','30s','2w','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management
portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fc207a1df4324fcf99ba1da262527fe3','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34454','20','1.3.6.1.4.1.318.1.1.1.1.2.3.0','10400','Serial number','system.sn[upsAdvIdentSerialNumber]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
An 8-character string identifying the serial number of
 the UPS internal microprocessor.  This number is set at
 the factory.  NOTE: This number does NOT correspond to
 the serial number on the rear of the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ef25b1e818534420920ff6260fa2932e','SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34455','20','1.3.6.1.2.1.1.2.0','10400','System object ID','system.objectid[sysObjectID.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management
subsystem contained in the entity.  This value is allocated within the SMI enterprises
subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what
kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was
assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1
to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5497f3649b9348dca290c55e94f48597','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34456','20','1.3.6.1.2.1.1.5.0','10400','System name','system.name[sysName.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
An administratively-assigned name for this managed node.By
convention, this is the node''s fully-qualified domain name.  If the name is unknown,
the value is the zero-length string.','3','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d6f2c9770c28487d9fa6af2b63917958','SYSTEM NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34457','20','1.3.6.1.4.1.318.1.1.1.1.1.1.0','10400','Model','system.model[upsBasicIdentModel]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS model name (e.g. ''APC Smart-UPS 600'').','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','93b6e128e95a4a96bde38ef15d74d510','MODEL');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34458','20','1.3.6.1.2.1.1.6.0','10400','System location','system.location[sysLocation.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet,
3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b109475e72e74e76846aa478e9937101','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34459','20','1.3.6.1.2.1.1.1.0','10400','System description','system.descr[sysDescr.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f1df592a2b114677a1beabec33ce01f9','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34460','20','1.3.6.1.2.1.1.4.0','10400','System contact details','system.contact[sysContact.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed
node, together with information on how to contact this person.  If no contact
information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','aa5e85ef78504fc080b97342baf6cb35','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34461','17','','10400','SNMP traps (fallback)','snmptrap.fallback','1m','2w','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'The item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7d20aa252c5143c98de837dbd2f0cd53','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34462','20','1.3.6.1.4.1.318.1.1.1.4.3.1.0','10400','Output voltage','output.voltage[upsHighPrecOutputVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The output voltage of the UPS system in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4ec893da7b8540548d60a91ee7e2df83','OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34463','20','1.3.6.1.4.1.318.1.1.1.4.3.3.0','10400','Output load','output.load[upsHighPrecOutputLoad]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current UPS load expressed as percentage
of rated capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5774ead79e8b4d63a4a31bc091d1c52a','OUTPUT LOAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34464','20','1.3.6.1.4.1.318.1.1.1.2.2.5.0','10400','External battery packs count','battery.external_packs_count[upsAdvBatteryNumOfBattPacks]','1h','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS. If
 the UPS does not use smart cells then the agent reports
 ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2b417eadc988460a89db04efdaca4ffc','EXTERNAL BATTERY PACKS COUNT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34465','20','1.3.6.1.4.1.318.1.1.1.4.3.4.0','10400','Output current','output.current[upsHighPrecOutputCurrent]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current in amperes drawn by the load on the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a6737781029b422ca7a8bbfa0ed80b56','OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34466','20','1.3.6.1.4.1.318.1.1.1.3.3.1.0','10400','Input voltage','input.voltage[upsHighPrecInputLineVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current utility line voltage in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','89bb663e356c4420bcbe2a9470ae3195','INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34467','20','1.3.6.1.4.1.318.1.1.1.3.3.4.0','10400','Input frequency','input.frequency[upsHighPrecInputFrequency]','1m','7d','365d','0','0','','Hz','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current input frequency to the UPS system in Hz.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3a64740655ca455ab0280592b5f0055f','INPUT FREQUENCY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34468','20','1.3.6.1.4.1.318.1.1.1.3.2.5.0','10400','Input fail cause','input.fail[upsAdvInputLineFailCause]','1m','7d','365d','0','3','','','','',NULL,'275','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The reason for the occurrence of the last transfer to UPS
battery power.  The variable is set to:
- noTransfer(1) -- if there is no transfer yet.
- highLineVoltage(2) -- if the transfer to battery is caused
by an over voltage greater than the high transfer voltage.
- brownout(3) -- if the duration of the outage is greater than
five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- blackout(4) -- if the duration of the outage is greater than five
seconds and the line voltage is between 40% of the rated
output voltage and ground.
- smallMomentarySag(5) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- deepMomentarySag(6) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and ground.  The variable is set to
- smallMomentarySpike(7) -- if the line failure is caused by a
rate of change of input voltage less than ten volts per cycle.
- largeMomentarySpike(8) -- if the line failure is caused by
a rate of change of input voltage greater than ten volts per cycle.
- selfTest(9) -- if the UPS was commanded to do a self test.
- rateOfVoltageChange(10) -- if the failure is due to the rate of change of
the line voltage.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9069a1c0d9304e7fa5f2df133dbb46cd','INPUT FAIL CAUSE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34469','20','1.3.6.1.4.1.318.1.1.1.2.3.4.0','10400','Battery voltage','battery.voltage[upsHighPrecBatteryActualVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The actual battery bus voltage in Volts.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','756f727fe8374aeba9d1afd7bbe77f02','BATTERY VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34470','20','1.3.6.1.4.1.318.1.1.1.2.3.2.0','10400','Battery temperature','battery.temperature[upsHighPrecBatteryTemperature]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current internal UPS temperature in Celsius.
 Temperatures below zero read as 0.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7a0a2b5e702f473fa1144eaf499367b2','BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34471','20','1.3.6.1.4.1.318.1.1.1.2.1.1.0','10400','Battery status','battery.status[upsBasicBatteryStatus]','1m','7d','365d','0','3','','','','',NULL,'276','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The status of the UPS batteries. A batteryLow(3) value
 indicates the UPS will be unable to sustain the current
 load, and its services will be lost if power is not restored.
 The amount of run time in reserve at the time of low battery
 can be configured by the upsAdvConfigLowBatteryRunTime.
 A batteryInFaultCondition(4)value indicates that a battery
 installed has an internal error condition.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','22a95e447ad74d43a191f368346fde59','BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34472','20','1.3.6.1.4.1.318.1.1.1.2.2.3.0','10400','Battery runtime remaining','battery.runtime_remaining[upsAdvBatteryRunTimeRemaining]','1m','7d','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS battery run time remaining before battery
 exhaustion.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','89cca909c60745fe824d02aa0d4bc3d7','BATTERY RUNTIME REMAINING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34473','20','1.3.6.1.4.1.318.1.1.1.2.2.4.0','10400','Battery replace indicator','battery.replace_indicator[upsAdvBatteryReplaceIndicator]','1m','7d','365d','0','3','','','','',NULL,'274','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
Indicates whether the UPS batteries need replacement.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b7614652ff6f4e0890f366b8e0831b80','BATTERY REPLACE INDICATOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34474','20','1.3.6.1.4.1.318.1.1.1.2.1.3.0','10400','Battery last replace date','battery.last_replace_date[upsBasicBatteryLastReplaceDate]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The date when the UPS system''s batteries were last replaced
 in mm/dd/yy (or yyyy) format. For Smart-UPS models, this value
 is originally set at the factory. When the UPS batteries
 are replaced, this value should be reset by the administrator.
 For Symmetra PX 250/500 this OID is read-only and is configurable in the local display only.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','98af792142464656b925a452e5ebf1cc','BATTERY LAST REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34475','5','','10400','SNMP agent availability','zabbix[host,snmp,available]','1m','7d','365d','0','3','','','','',NULL,'278','','','0','','','','','0',NULL,'Availability of SNMP checks on the host. The value of this item corresponds to availability icons in the host list.
Possible value:
0 - not available
1 - available
2 - unknown','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','efad5c028c0d4c11b57a19dc04830ea7','SNMP AGENT AVAILABILITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34476','20','discovery[{#EXTERNAL_PACKS},1.3.6.1.4.1.318.1.1.1.2.2.6]','10400','External bad battery packs discovery','battery.packs.bad.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of the number of external defective battery packs.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','54a867c14c814e4ab4803c5a59082e44','EXTERNAL BAD BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34477','20','discovery[{#CARTRIDGE_STATUS},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7,{#BATTERY_PACK},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.1,{#CARTRIDGE_INDEX},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.2]','10400','External battery packs discovery','battery.packs.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0c8fc55bbe984d919c3b87a096d900d5','EXTERNAL BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34478','20','discovery[{#EXTERNAL_SENSOR1_NAME},1.3.6.1.4.1.318.1.1.25.1.2.1.3]','10400','External sensor port 1 discovery','external.sensor1.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ffb60da941114174932b219e14892be9','EXTERNAL SENSOR PORT 1 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34479','20','discovery[{#EXTERNAL_SENSOR2_NAME},1.3.6.1.4.1.318.1.1.25.1.2.2.3]','10400','External sensor port 2 discovery','external.sensor2.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','463ed9f01f3a4cf6ba91f2707baded15','EXTERNAL SENSOR PORT 2 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34480','20','discovery[{#PHASEINDEX},1.3.6.1.4.1.318.1.1.1.9.2.3.1.2.1.1]','10400','Input phases discovery','input.phases.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The input phase identifier. OID upsPhaseInputPhaseIndex.1.1','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f16f2ab100614ae6bccf66e5a840c7db','INPUT PHASES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34481','20','discovery[{#PHASEINDEX},1.3.6.1.4.1.318.1.1.1.9.3.3.1.2.1.1]','10400','Output phases discovery','output.phases.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The output phase identifier. OID upsPhaseOutputPhaseIndex.1.1','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','518ca26562f04d7b8e5af9d26317d138','OUTPUT PHASES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34482','20','1.3.6.1.4.1.318.1.1.1.2.2.6.0','10400','{#SNMPINDEX}: External battery packs bad','battery.external_packs_bad[upsAdvBatteryNumOfBadBattPacks.{#SNMPINDEX}]','15m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS that
are defective. If the UPS does not use smart cells then the
agent reports ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2a60e35fabb44c78bd827e22293166d9','{#SNMPINDEX}: EXTERNAL BATTERY PACKS BAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34483','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.8.{#SNMPINDEX}','10400','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery estimated replace date','battery.estimated_replace_date[upsHighPrecBatteryPackCartridgeReplaceDate.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge estimated battery replace date.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a7023eed55484d1d9f0754ccb1ec9f87','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY ESTIMATED REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34484','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7.{#SNMPINDEX}','10400','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery pack cartridge health','battery.pack.cartridge_health[upsHighPrecBatteryPackCartridgeHealth.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge health.
  bit 0 Battery lifetime okay
  bit 1 Battery lifetime near end, order replacement cartridge
  bit 2 Battery lifetime exceeded, replace battery
  bit 3 Battery lifetime near end acknowledged, order replacement cartridge
  bit 4 Battery lifetime exceeded acknowledged, replace battery
  bit 5 Battery measured lifetime near end, order replacement cartridge
  bit 6 Battery measured lifetime near end acknowledged, order replacement cartridge','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','41cd82bb312344b7bdb9c7c5aac2eb21','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY PACK CARTRIDGE HEALTH');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34485','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.10.{#SNMPINDEX}','10400','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery status','battery.pack.status[upsHighPrecBatteryPackCartridgeStatus.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge status.
bit 0 Disconnected
bit 1 Overvoltage
bit 2 NeedsReplacement
bit 3 OvertemperatureCritical
bit 4 Charger
bit 5 TemperatureSensor
bit 6 BusSoftStart
bit 7 OvertemperatureWarning
bit 8 GeneralError
bit 9 Communication
bit 10 DisconnectedFrame
bit 11 FirmwareMismatch','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','241efd4ef6204c58adc04e4e04660845','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34486','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.5.{#SNMPINDEX}','10400','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery temperature','battery.temperature[upsHighPrecBatteryPackTemperature.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack temperature in Celsius.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a55dd3033a2645aab5592f356043c342','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34487','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.4.{#SNMPINDEX}','10400','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Serial number','system.sn[upsHighPrecBatteryPackSerialNumber.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack serial number.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','8ea7d066a5ae4141b4cd0af13d96c40c','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34488','20','1.3.6.1.4.1.318.1.1.25.1.2.1.7.1.1','10400','{#EXTERNAL_SENSOR1_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f2bcca2221e94e828755a90f98c98495','{#EXTERNAL_SENSOR1_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34489','20','1.3.6.1.4.1.318.1.1.25.1.2.1.9.1.1','10400','{#EXTERNAL_SENSOR1_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.1.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'273','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1a41c120082948bdb6865413bdc09917','{#EXTERNAL_SENSOR1_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34490','20','1.3.6.1.4.1.318.1.1.25.1.2.1.6.1.1','10400','{#EXTERNAL_SENSOR1_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a191d2ff066e4f4ba04aede67cd6876d','{#EXTERNAL_SENSOR1_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34491','20','1.3.6.1.4.1.318.1.1.25.1.2.2.7.1.1','10400','{#EXTERNAL_SENSOR2_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e2200965a13541b1a100e4880d8363ff','{#EXTERNAL_SENSOR2_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34492','20','1.3.6.1.4.1.318.1.1.25.1.2.2.9.1.1','10400','{#EXTERNAL_SENSOR2_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.2.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'273','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','492835d959d644d7b95fc480cba5d3dc','{#EXTERNAL_SENSOR2_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34493','20','1.3.6.1.4.1.318.1.1.25.1.2.2.6.1.1','10400','{#EXTERNAL_SENSOR2_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2cf2d697c95845ba8ec61af2ec698f4c','{#EXTERNAL_SENSOR2_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34494','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.6.1.1.{#PHASEINDEX}','10400','{#PHASEINDEX}: Phase input current','phase.input.current[upsPhaseInputCurrent.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input current in 0.1 amperes, or -0.1 if it''s
 unsupported by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7c0490500bed4258a8663777cd62e378','{#PHASEINDEX}: PHASE INPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34495','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.3.1.1.{#PHASEINDEX}','10400','{#PHASEINDEX}: Phase input voltage','phase.input.voltage[upsPhaseInputVoltage.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input voltage in VAC, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7356945fc0e94026a2ca04d297fdf953','{#PHASEINDEX}: PHASE INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34496','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.4.1.1.{#PHASEINDEX}','10400','{#PHASEINDEX}: Phase output current','phase.output.current[upsPhaseOutputCurrent.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The output current in 0.1 amperes drawn
 by the load on the UPS, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c3888f41e7f246b1a30d21325f814695','{#PHASEINDEX}: PHASE OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34497','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.10.1.1.{#PHASEINDEX}','10400','{#PHASEINDEX}: Phase output load, %','phase.output.load.percent[upsPhaseOutputPercentLoad.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The percentage of the UPS load capacity in VA at
 redundancy @ (n + x) presently being used on this
 output phase, or -1 if it''s unsupported by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3eb001cece8340d59cd0e7f59812f149','{#PHASEINDEX}: PHASE OUTPUT LOAD, %');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34498','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.3.1.1.{#PHASEINDEX}','10400','{#PHASEINDEX}: Phase output voltage','phase.output.voltage[upsPhaseOutputVoltage.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The output voltage in VAC, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f09e23dcb5b24170b356556a36bb39cc','{#PHASEINDEX}: PHASE OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34499','20','1.3.6.1.4.1.318.1.1.1.2.3.1.0','10401','Battery capacity','battery.capacity[upsHighPrecBatteryCapacity]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The remaining battery capacity expressed as
 percentage of full capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6933bd19628f4699974d5dc4b1637c53','BATTERY CAPACITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34500','20','1.3.6.1.4.1.318.1.1.1.4.1.1.0','10401','Output status','output.status[upsBasicOutputStatus]','1m','7d','365d','0','3','','','','',NULL,'283','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current state of the UPS. If the UPS is unable to
 determine the state of the UPS this variable is set
 to unknown(1).
During self-test most UPSes report onBattery(3) but
 some that support it will report onBatteryTest(15).
 To determine self-test status across all UPSes, refer
 to the upsBasicStateOutputState OID.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','54d22d1cc362492ebe8695257afc20ec','OUTPUT STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34501','20','1.3.6.1.2.1.1.3.0','10401','Uptime (network)','system.net.uptime[sysUpTime.0]','30s','2w','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management
portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f077c3558d24471ca807ea24b3f0c5ea','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34502','20','1.3.6.1.4.1.318.1.1.1.1.2.3.0','10401','Serial number','system.sn[upsAdvIdentSerialNumber]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
An 8-character string identifying the serial number of
 the UPS internal microprocessor.  This number is set at
 the factory.  NOTE: This number does NOT correspond to
 the serial number on the rear of the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4e87619ed81346d497c3c3f548c342b5','SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34503','20','1.3.6.1.2.1.1.2.0','10401','System object ID','system.objectid[sysObjectID.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management
subsystem contained in the entity.  This value is allocated within the SMI enterprises
subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what
kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was
assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1
to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5a393860311b4b64ae5a4ce7cd7000dc','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34504','20','1.3.6.1.2.1.1.5.0','10401','System name','system.name[sysName.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
An administratively-assigned name for this managed node.By
convention, this is the node''s fully-qualified domain name.  If the name is unknown,
the value is the zero-length string.','3','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d9452c921e4946719726b292d8c0cbd6','SYSTEM NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34505','20','1.3.6.1.4.1.318.1.1.1.1.1.1.0','10401','Model','system.model[upsBasicIdentModel]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS model name (e.g. ''APC Smart-UPS 600'').','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1ba45d867e3d4bb99eeb8c0c320ef127','MODEL');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34506','20','1.3.6.1.2.1.1.6.0','10401','System location','system.location[sysLocation.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet,
3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ac995904f95240d9b1f44c27adea5731','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34507','20','1.3.6.1.2.1.1.1.0','10401','System description','system.descr[sysDescr.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e5d72eba4dfb41f8ae73904c936dd64b','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34508','20','1.3.6.1.2.1.1.4.0','10401','System contact details','system.contact[sysContact.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed
node, together with information on how to contact this person.  If no contact
information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','943b146891ac461c92d286704a0864b2','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34509','17','','10401','SNMP traps (fallback)','snmptrap.fallback','1m','2w','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'The item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','94d838cc8cf2438296477c0139a3c152','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34510','20','1.3.6.1.4.1.318.1.1.1.4.3.1.0','10401','Output voltage','output.voltage[upsHighPrecOutputVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The output voltage of the UPS system in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4e43a6966bf642e19567dcd3763125e7','OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34511','20','1.3.6.1.4.1.318.1.1.1.4.3.3.0','10401','Output load','output.load[upsHighPrecOutputLoad]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current UPS load expressed as percentage
of rated capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','df799c65dbe5437aa941de3e6d386b26','OUTPUT LOAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34512','20','1.3.6.1.4.1.318.1.1.1.2.2.5.0','10401','External battery packs count','battery.external_packs_count[upsAdvBatteryNumOfBattPacks]','1h','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS. If
 the UPS does not use smart cells then the agent reports
 ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','8ba1d824fdc548b4bca770f4145f7169','EXTERNAL BATTERY PACKS COUNT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34513','20','1.3.6.1.4.1.318.1.1.1.4.3.4.0','10401','Output current','output.current[upsHighPrecOutputCurrent]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current in amperes drawn by the load on the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','744d345cd3964baf85f8fefed19f9001','OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34514','20','1.3.6.1.4.1.318.1.1.1.3.3.1.0','10401','Input voltage','input.voltage[upsHighPrecInputLineVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current utility line voltage in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','91a6bc765a954f9e97b855d9dfebd3f7','INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34515','20','1.3.6.1.4.1.318.1.1.1.3.3.4.0','10401','Input frequency','input.frequency[upsHighPrecInputFrequency]','1m','7d','365d','0','0','','Hz','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current input frequency to the UPS system in Hz.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','cfd390d57dbc4046a3a6af384420b697','INPUT FREQUENCY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34516','20','1.3.6.1.4.1.318.1.1.1.3.2.5.0','10401','Input fail cause','input.fail[upsAdvInputLineFailCause]','1m','7d','365d','0','3','','','','',NULL,'281','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The reason for the occurrence of the last transfer to UPS
battery power.  The variable is set to:
- noTransfer(1) -- if there is no transfer yet.
- highLineVoltage(2) -- if the transfer to battery is caused
by an over voltage greater than the high transfer voltage.
- brownout(3) -- if the duration of the outage is greater than
five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- blackout(4) -- if the duration of the outage is greater than five
seconds and the line voltage is between 40% of the rated
output voltage and ground.
- smallMomentarySag(5) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- deepMomentarySag(6) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and ground.  The variable is set to
- smallMomentarySpike(7) -- if the line failure is caused by a
rate of change of input voltage less than ten volts per cycle.
- largeMomentarySpike(8) -- if the line failure is caused by
a rate of change of input voltage greater than ten volts per cycle.
- selfTest(9) -- if the UPS was commanded to do a self test.
- rateOfVoltageChange(10) -- if the failure is due to the rate of change of
the line voltage.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b83275fc1176451dacaa28606edf045a','INPUT FAIL CAUSE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34517','20','1.3.6.1.4.1.318.1.1.1.2.3.4.0','10401','Battery voltage','battery.voltage[upsHighPrecBatteryActualVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The actual battery bus voltage in Volts.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','805d95a6f256410ca083f31cc480b88b','BATTERY VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34518','20','1.3.6.1.4.1.318.1.1.1.2.3.2.0','10401','Battery temperature','battery.temperature[upsHighPrecBatteryTemperature]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current internal UPS temperature in Celsius.
 Temperatures below zero read as 0.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','bda8df2bbd2a40dc937b2cd5b8017a68','BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34519','20','1.3.6.1.4.1.318.1.1.1.2.1.1.0','10401','Battery status','battery.status[upsBasicBatteryStatus]','1m','7d','365d','0','3','','','','',NULL,'282','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The status of the UPS batteries. A batteryLow(3) value
 indicates the UPS will be unable to sustain the current
 load, and its services will be lost if power is not restored.
 The amount of run time in reserve at the time of low battery
 can be configured by the upsAdvConfigLowBatteryRunTime.
 A batteryInFaultCondition(4)value indicates that a battery
 installed has an internal error condition.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','078719d0396247bca76d85e1e4c650de','BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34520','20','1.3.6.1.4.1.318.1.1.1.2.2.3.0','10401','Battery runtime remaining','battery.runtime_remaining[upsAdvBatteryRunTimeRemaining]','1m','7d','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS battery run time remaining before battery
 exhaustion.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','05be71fcb7c1484f876229f48649039e','BATTERY RUNTIME REMAINING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34521','20','1.3.6.1.4.1.318.1.1.1.2.2.4.0','10401','Battery replace indicator','battery.replace_indicator[upsAdvBatteryReplaceIndicator]','1m','7d','365d','0','3','','','','',NULL,'280','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
Indicates whether the UPS batteries need replacement.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4c1107eb93114d9096518dc134e08bdc','BATTERY REPLACE INDICATOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34522','20','1.3.6.1.4.1.318.1.1.1.2.1.3.0','10401','Battery last replace date','battery.last_replace_date[upsBasicBatteryLastReplaceDate]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The date when the UPS system''s batteries were last replaced
 in mm/dd/yy (or yyyy) format. For Smart-UPS models, this value
 is originally set at the factory. When the UPS batteries
 are replaced, this value should be reset by the administrator.
 For Symmetra PX 250/500 this OID is read-only and is configurable in the local display only.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','147e0b7b466e402ba59d73d66801ef1a','BATTERY LAST REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34523','5','','10401','SNMP agent availability','zabbix[host,snmp,available]','1m','7d','365d','0','3','','','','',NULL,'284','','','0','','','','','0',NULL,'Availability of SNMP checks on the host. The value of this item corresponds to availability icons in the host list.
Possible value:
0 - not available
1 - available
2 - unknown','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d679688992124f6c91c3f70bcc341d2d','SNMP AGENT AVAILABILITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34524','20','discovery[{#EXTERNAL_PACKS},1.3.6.1.4.1.318.1.1.1.2.2.6]','10401','External bad battery packs discovery','battery.packs.bad.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of the number of external defective battery packs.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','72077c26a51b43a6afea271e70d13004','EXTERNAL BAD BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34525','20','discovery[{#CARTRIDGE_STATUS},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7,{#BATTERY_PACK},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.1,{#CARTRIDGE_INDEX},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.2]','10401','External battery packs discovery','battery.packs.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','38aa32616e964db088f4faff12867f1a','EXTERNAL BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34526','20','discovery[{#EXTERNAL_SENSOR1_NAME},1.3.6.1.4.1.318.1.1.25.1.2.1.3]','10401','External sensor port 1 discovery','external.sensor1.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e428310ecc5f4a53ab7932bcf1247a30','EXTERNAL SENSOR PORT 1 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34527','20','discovery[{#EXTERNAL_SENSOR2_NAME},1.3.6.1.4.1.318.1.1.25.1.2.2.3]','10401','External sensor port 2 discovery','external.sensor2.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','291c45432792490fb3dbccab1a0b9183','EXTERNAL SENSOR PORT 2 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34528','20','discovery[{#PHASEINDEX},1.3.6.1.4.1.318.1.1.1.9.2.3.1.2.1.1]','10401','Input phases discovery','input.phases.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The input phase identifier. OID upsPhaseInputPhaseIndex.1.1','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f39e3c1e6b774ada90ca722cb6ca59b4','INPUT PHASES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34529','20','discovery[{#PHASEINDEX},1.3.6.1.4.1.318.1.1.1.9.3.3.1.2.1.1]','10401','Output phases discovery','output.phases.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The output phase identifier. OID upsPhaseOutputPhaseIndex.1.1','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f56bcd41c5ee4e16b2558563718bf2a6','OUTPUT PHASES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34530','20','1.3.6.1.4.1.318.1.1.1.2.2.6.0','10401','{#SNMPINDEX}: External battery packs bad','battery.external_packs_bad[upsAdvBatteryNumOfBadBattPacks.{#SNMPINDEX}]','15m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS that
are defective. If the UPS does not use smart cells then the
agent reports ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','76ae1be14ab6402e9495bf0dea6243f2','{#SNMPINDEX}: EXTERNAL BATTERY PACKS BAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34531','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.8.{#SNMPINDEX}','10401','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery estimated replace date','battery.estimated_replace_date[upsHighPrecBatteryPackCartridgeReplaceDate.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge estimated battery replace date.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','153ab66e45ae4bc3bbf33324c111ea5e','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY ESTIMATED REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34532','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7.{#SNMPINDEX}','10401','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery pack cartridge health','battery.pack.cartridge_health[upsHighPrecBatteryPackCartridgeHealth.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge health.
  bit 0 Battery lifetime okay
  bit 1 Battery lifetime near end, order replacement cartridge
  bit 2 Battery lifetime exceeded, replace battery
  bit 3 Battery lifetime near end acknowledged, order replacement cartridge
  bit 4 Battery lifetime exceeded acknowledged, replace battery
  bit 5 Battery measured lifetime near end, order replacement cartridge
  bit 6 Battery measured lifetime near end acknowledged, order replacement cartridge','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2e3adbdd7c9a4f3f9f151d19e69885bf','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY PACK CARTRIDGE HEALTH');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34533','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.10.{#SNMPINDEX}','10401','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery status','battery.pack.status[upsHighPrecBatteryPackCartridgeStatus.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge status.
bit 0 Disconnected
bit 1 Overvoltage
bit 2 NeedsReplacement
bit 3 OvertemperatureCritical
bit 4 Charger
bit 5 TemperatureSensor
bit 6 BusSoftStart
bit 7 OvertemperatureWarning
bit 8 GeneralError
bit 9 Communication
bit 10 DisconnectedFrame
bit 11 FirmwareMismatch','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','90e566dbc3184ef8b2ff171630a37c8a','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34534','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.5.{#SNMPINDEX}','10401','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery temperature','battery.temperature[upsHighPrecBatteryPackTemperature.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack temperature in Celsius.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9277c9b4e065400eb31f2ad965bfa2a5','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34535','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.4.{#SNMPINDEX}','10401','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Serial number','system.sn[upsHighPrecBatteryPackSerialNumber.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack serial number.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','70a45fc5ad1945a89133a4729340bdee','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34536','20','1.3.6.1.4.1.318.1.1.25.1.2.1.7.1.1','10401','{#EXTERNAL_SENSOR1_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','5bc38e9b268047e09d77fc144395b2df','{#EXTERNAL_SENSOR1_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34537','20','1.3.6.1.4.1.318.1.1.25.1.2.1.9.1.1','10401','{#EXTERNAL_SENSOR1_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.1.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'279','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c4bd5c3b0af145448aa2b084738f5149','{#EXTERNAL_SENSOR1_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34538','20','1.3.6.1.4.1.318.1.1.25.1.2.1.6.1.1','10401','{#EXTERNAL_SENSOR1_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','87494b17faf349248ed6cffc4c932a0f','{#EXTERNAL_SENSOR1_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34539','20','1.3.6.1.4.1.318.1.1.25.1.2.2.7.1.1','10401','{#EXTERNAL_SENSOR2_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e2cbe8a1fdfe4d368987a8417dc5637b','{#EXTERNAL_SENSOR2_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34540','20','1.3.6.1.4.1.318.1.1.25.1.2.2.9.1.1','10401','{#EXTERNAL_SENSOR2_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.2.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'279','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fc4623c5e962448dbffc98301ddcef4b','{#EXTERNAL_SENSOR2_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34541','20','1.3.6.1.4.1.318.1.1.25.1.2.2.6.1.1','10401','{#EXTERNAL_SENSOR2_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b4e350ad5bb24d7b96091f8b9766cff7','{#EXTERNAL_SENSOR2_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34542','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.6.1.1.{#PHASEINDEX}','10401','{#PHASEINDEX}: Phase input current','phase.input.current[upsPhaseInputCurrent.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input current in 0.1 amperes, or -0.1 if it''s
 unsupported by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2be0a7af3cd34723aa5560cd0f86cb44','{#PHASEINDEX}: PHASE INPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34543','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.3.1.1.{#PHASEINDEX}','10401','{#PHASEINDEX}: Phase input voltage','phase.input.voltage[upsPhaseInputVoltage.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input voltage in VAC, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','dac612b382ce4b93b588e2ba43c01c68','{#PHASEINDEX}: PHASE INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34544','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.4.1.1.{#PHASEINDEX}','10401','{#PHASEINDEX}: Phase output current','phase.output.current[upsPhaseOutputCurrent.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The output current in 0.1 amperes drawn
 by the load on the UPS, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','193b0c6624a44545b28009ab31463125','{#PHASEINDEX}: PHASE OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34545','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.10.1.1.{#PHASEINDEX}','10401','{#PHASEINDEX}: Phase output load, %','phase.output.load.percent[upsPhaseOutputPercentLoad.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The percentage of the UPS load capacity in VA at
 redundancy @ (n + x) presently being used on this
 output phase, or -1 if it''s unsupported by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3af338de874c439daeba535156033317','{#PHASEINDEX}: PHASE OUTPUT LOAD, %');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34546','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.3.1.1.{#PHASEINDEX}','10401','{#PHASEINDEX}: Phase output voltage','phase.output.voltage[upsPhaseOutputVoltage.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The output voltage in VAC, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a7aecf3b0c2e448b9c09babc79c52380','{#PHASEINDEX}: PHASE OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34547','20','1.3.6.1.4.1.318.1.1.1.2.3.1.0','10402','Battery capacity','battery.capacity[upsHighPrecBatteryCapacity]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The remaining battery capacity expressed as
 percentage of full capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6e8ed2c349d744a1a07928b32cf574c3','BATTERY CAPACITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34548','20','1.3.6.1.4.1.318.1.1.1.4.1.1.0','10402','Output status','output.status[upsBasicOutputStatus]','1m','7d','365d','0','3','','','','',NULL,'289','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current state of the UPS. If the UPS is unable to
 determine the state of the UPS this variable is set
 to unknown(1).
During self-test most UPSes report onBattery(3) but
 some that support it will report onBatteryTest(15).
 To determine self-test status across all UPSes, refer
 to the upsBasicStateOutputState OID.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','107461ac37984a708acf7f55ae248d67','OUTPUT STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34549','20','1.3.6.1.2.1.1.3.0','10402','Uptime (network)','system.net.uptime[sysUpTime.0]','30s','2w','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management
portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','39dd6b9b815a4a838a43d2ebf3fcc8f9','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34550','20','1.3.6.1.4.1.318.1.1.1.1.2.3.0','10402','Serial number','system.sn[upsAdvIdentSerialNumber]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
An 8-character string identifying the serial number of
 the UPS internal microprocessor.  This number is set at
 the factory.  NOTE: This number does NOT correspond to
 the serial number on the rear of the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0c36d0bb59a44db2b80ae4a4ff2d7c1b','SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34551','20','1.3.6.1.2.1.1.2.0','10402','System object ID','system.objectid[sysObjectID.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management
subsystem contained in the entity.  This value is allocated within the SMI enterprises
subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what
kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was
assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1
to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f6922cd0f93a4a4288a978ff8336226b','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34552','20','1.3.6.1.2.1.1.5.0','10402','System name','system.name[sysName.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
An administratively-assigned name for this managed node.By
convention, this is the node''s fully-qualified domain name.  If the name is unknown,
the value is the zero-length string.','3','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1f591627fea54a9ebdd8f10cbf39b9ed','SYSTEM NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34553','20','1.3.6.1.4.1.318.1.1.1.1.1.1.0','10402','Model','system.model[upsBasicIdentModel]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS model name (e.g. ''APC Smart-UPS 600'').','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','272883d0a1cd4bb585a6ede50336c873','MODEL');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34554','20','1.3.6.1.2.1.1.6.0','10402','System location','system.location[sysLocation.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet,
3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a5c6c4c44132439abd0e5fd88e3c90cf','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34555','20','1.3.6.1.2.1.1.1.0','10402','System description','system.descr[sysDescr.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a312df9175ca45528375398f56fa3b3b','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34556','20','1.3.6.1.2.1.1.4.0','10402','System contact details','system.contact[sysContact.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed
node, together with information on how to contact this person.  If no contact
information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','fbcbe2cffc8c4bb6b11276cdd03376c3','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34557','17','','10402','SNMP traps (fallback)','snmptrap.fallback','1m','2w','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'The item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','92c2ef138bf148199cdb6d9684b6fa23','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34558','20','1.3.6.1.4.1.318.1.1.1.4.3.1.0','10402','Output voltage','output.voltage[upsHighPrecOutputVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The output voltage of the UPS system in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ebf71f0afed5460ba4c7f66bb162de9f','OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34559','20','1.3.6.1.4.1.318.1.1.1.4.3.3.0','10402','Output load','output.load[upsHighPrecOutputLoad]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current UPS load expressed as percentage
of rated capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a2613c8d71864594a0c94064d99e059e','OUTPUT LOAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34560','20','1.3.6.1.4.1.318.1.1.1.2.2.5.0','10402','External battery packs count','battery.external_packs_count[upsAdvBatteryNumOfBattPacks]','1h','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS. If
 the UPS does not use smart cells then the agent reports
 ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','86780568c0594469bc7324c68440cbec','EXTERNAL BATTERY PACKS COUNT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34561','20','1.3.6.1.4.1.318.1.1.1.4.3.4.0','10402','Output current','output.current[upsHighPrecOutputCurrent]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current in amperes drawn by the load on the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a8d017e0fa5d4eca838ad068f0dffcd9','OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34562','20','1.3.6.1.4.1.318.1.1.1.3.3.1.0','10402','Input voltage','input.voltage[upsHighPrecInputLineVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current utility line voltage in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e90dbc034cc447afb4ac1c8ced484882','INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34563','20','1.3.6.1.4.1.318.1.1.1.3.3.4.0','10402','Input frequency','input.frequency[upsHighPrecInputFrequency]','1m','7d','365d','0','0','','Hz','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current input frequency to the UPS system in Hz.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ab28b72c192e48b5819079bd386ba8ea','INPUT FREQUENCY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34564','20','1.3.6.1.4.1.318.1.1.1.3.2.5.0','10402','Input fail cause','input.fail[upsAdvInputLineFailCause]','1m','7d','365d','0','3','','','','',NULL,'287','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The reason for the occurrence of the last transfer to UPS
battery power.  The variable is set to:
- noTransfer(1) -- if there is no transfer yet.
- highLineVoltage(2) -- if the transfer to battery is caused
by an over voltage greater than the high transfer voltage.
- brownout(3) -- if the duration of the outage is greater than
five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- blackout(4) -- if the duration of the outage is greater than five
seconds and the line voltage is between 40% of the rated
output voltage and ground.
- smallMomentarySag(5) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- deepMomentarySag(6) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and ground.  The variable is set to
- smallMomentarySpike(7) -- if the line failure is caused by a
rate of change of input voltage less than ten volts per cycle.
- largeMomentarySpike(8) -- if the line failure is caused by
a rate of change of input voltage greater than ten volts per cycle.
- selfTest(9) -- if the UPS was commanded to do a self test.
- rateOfVoltageChange(10) -- if the failure is due to the rate of change of
the line voltage.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7b7d6fdeea2e49c9bb74eb301ecca93a','INPUT FAIL CAUSE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34565','20','1.3.6.1.4.1.318.1.1.1.2.3.4.0','10402','Battery voltage','battery.voltage[upsHighPrecBatteryActualVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The actual battery bus voltage in Volts.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','e478bdaa89674f6792e39ff1a2d9a413','BATTERY VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34566','20','1.3.6.1.4.1.318.1.1.1.2.3.2.0','10402','Battery temperature','battery.temperature[upsHighPrecBatteryTemperature]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current internal UPS temperature in Celsius.
 Temperatures below zero read as 0.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','bded43c8a4eb4d1b9cf5403d3f3027cd','BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34567','20','1.3.6.1.4.1.318.1.1.1.2.1.1.0','10402','Battery status','battery.status[upsBasicBatteryStatus]','1m','7d','365d','0','3','','','','',NULL,'288','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The status of the UPS batteries. A batteryLow(3) value
 indicates the UPS will be unable to sustain the current
 load, and its services will be lost if power is not restored.
 The amount of run time in reserve at the time of low battery
 can be configured by the upsAdvConfigLowBatteryRunTime.
 A batteryInFaultCondition(4)value indicates that a battery
 installed has an internal error condition.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','9fa77fdcbd7343ca904c6282efcb7c72','BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34568','20','1.3.6.1.4.1.318.1.1.1.2.2.3.0','10402','Battery runtime remaining','battery.runtime_remaining[upsAdvBatteryRunTimeRemaining]','1m','7d','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS battery run time remaining before battery
 exhaustion.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d15c36fb66754791b1014f52171efe1c','BATTERY RUNTIME REMAINING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34569','20','1.3.6.1.4.1.318.1.1.1.2.2.4.0','10402','Battery replace indicator','battery.replace_indicator[upsAdvBatteryReplaceIndicator]','1m','7d','365d','0','3','','','','',NULL,'286','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
Indicates whether the UPS batteries need replacement.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b50a17ab043c404990dd088ac9f74078','BATTERY REPLACE INDICATOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34570','20','1.3.6.1.4.1.318.1.1.1.2.1.3.0','10402','Battery last replace date','battery.last_replace_date[upsBasicBatteryLastReplaceDate]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The date when the UPS system''s batteries were last replaced
 in mm/dd/yy (or yyyy) format. For Smart-UPS models, this value
 is originally set at the factory. When the UPS batteries
 are replaced, this value should be reset by the administrator.
 For Symmetra PX 250/500 this OID is read-only and is configurable in the local display only.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1928e58e65a34b188916086bad5b8725','BATTERY LAST REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34571','5','','10402','SNMP agent availability','zabbix[host,snmp,available]','1m','7d','365d','0','3','','','','',NULL,'290','','','0','','','','','0',NULL,'Availability of SNMP checks on the host. The value of this item corresponds to availability icons in the host list.
Possible value:
0 - not available
1 - available
2 - unknown','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','edb39f7236d74c6783e0d4b832e0b94b','SNMP AGENT AVAILABILITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34572','20','discovery[{#EXTERNAL_PACKS},1.3.6.1.4.1.318.1.1.1.2.2.6]','10402','External bad battery packs discovery','battery.packs.bad.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'Discovery of the number of external defective battery packs.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','2edf8773186845499a991288d1a7a55b','EXTERNAL BAD BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34573','20','discovery[{#CARTRIDGE_STATUS},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7,{#BATTERY_PACK},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.1,{#CARTRIDGE_INDEX},1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.2]','10402','External battery packs discovery','battery.packs.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'','0','30d','1','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a0d8d681bfb54c1d9792beaf3f708d69','EXTERNAL BATTERY PACKS DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34574','20','discovery[{#EXTERNAL_SENSOR1_NAME},1.3.6.1.4.1.318.1.1.25.1.2.1.3]','10402','External sensor port 1 discovery','external.sensor1.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','88f5bc98004740fe886f5b1144de2c35','EXTERNAL SENSOR PORT 1 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34575','20','discovery[{#EXTERNAL_SENSOR2_NAME},1.3.6.1.4.1.318.1.1.25.1.2.2.3]','10402','External sensor port 2 discovery','external.sensor2.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'uioSensorStatusTable','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c64b5cb02dec4873a2e041359da3cdf7','EXTERNAL SENSOR PORT 2 DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34576','20','discovery[{#PHASEINDEX},1.3.6.1.4.1.318.1.1.1.9.2.3.1.2.1.1]','10402','Input phases discovery','input.phases.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The input phase identifier. OID upsPhaseInputPhaseIndex.1.1','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','ecca1791b7744f30bfcc1018a10cf1fa','INPUT PHASES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34577','20','discovery[{#PHASEINDEX},1.3.6.1.4.1.318.1.1.1.9.3.3.1.2.1.1]','10402','Output phases discovery','output.phases.discovery','1h','90d','0','0','4','','','','',NULL,NULL,'','','0','','','','','1',NULL,'The output phase identifier. OID upsPhaseOutputPhaseIndex.1.1','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c1771434bf6b476280c2f2d15bb52608','OUTPUT PHASES DISCOVERY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34578','20','1.3.6.1.4.1.318.1.1.1.2.2.6.0','10402','{#SNMPINDEX}: External battery packs bad','battery.external_packs_bad[upsAdvBatteryNumOfBadBattPacks.{#SNMPINDEX}]','15m','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS that
are defective. If the UPS does not use smart cells then the
agent reports ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7ff04c0f873c4c0f9af5aca2bd447cce','{#SNMPINDEX}: EXTERNAL BATTERY PACKS BAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34579','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.8.{#SNMPINDEX}','10402','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery estimated replace date','battery.estimated_replace_date[upsHighPrecBatteryPackCartridgeReplaceDate.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge estimated battery replace date.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','35e7da4783e245a2bfff75f3ae79ff5e','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY ESTIMATED REPLACE DATE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34580','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.7.{#SNMPINDEX}','10402','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery pack cartridge health','battery.pack.cartridge_health[upsHighPrecBatteryPackCartridgeHealth.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge health.
  bit 0 Battery lifetime okay
  bit 1 Battery lifetime near end, order replacement cartridge
  bit 2 Battery lifetime exceeded, replace battery
  bit 3 Battery lifetime near end acknowledged, order replacement cartridge
  bit 4 Battery lifetime exceeded acknowledged, replace battery
  bit 5 Battery measured lifetime near end, order replacement cartridge
  bit 6 Battery measured lifetime near end acknowledged, order replacement cartridge','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','b86ac9ee81fe40c8995618c387775270','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY PACK CARTRIDGE HEALTH');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34581','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.10.{#SNMPINDEX}','10402','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery status','battery.pack.status[upsHighPrecBatteryPackCartridgeStatus.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery cartridge status.
bit 0 Disconnected
bit 1 Overvoltage
bit 2 NeedsReplacement
bit 3 OvertemperatureCritical
bit 4 Charger
bit 5 TemperatureSensor
bit 6 BusSoftStart
bit 7 OvertemperatureWarning
bit 8 GeneralError
bit 9 Communication
bit 10 DisconnectedFrame
bit 11 FirmwareMismatch','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','db78c715c220433cb338199d43cb84a0','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34582','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.5.{#SNMPINDEX}','10402','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Battery temperature','battery.temperature[upsHighPrecBatteryPackTemperature.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack temperature in Celsius.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','bab950aa54ca425db4593049a64cf56f','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34583','20','1.3.6.1.4.1.318.1.1.1.2.3.10.2.1.4.{#SNMPINDEX}','10402','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: Serial number','system.sn[upsHighPrecBatteryPackSerialNumber.{#BATTERY_PACK}.{#CARTRIDGE_INDEX}]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The battery pack serial number.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d2983b402dfd4435a4790d560da8f6f6','{#BATTERY_PACK}.{#CARTRIDGE_INDEX}: SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34584','20','1.3.6.1.4.1.318.1.1.25.1.2.1.7.1.1','10402','{#EXTERNAL_SENSOR1_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','34e5f00097f4448eadf16071cfa234e9','{#EXTERNAL_SENSOR1_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34585','20','1.3.6.1.4.1.318.1.1.25.1.2.1.9.1.1','10402','{#EXTERNAL_SENSOR1_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.1.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'285','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','04425d6cc153491d9cb710b875f8c9cb','{#EXTERNAL_SENSOR1_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34586','20','1.3.6.1.4.1.318.1.1.25.1.2.1.6.1.1','10402','{#EXTERNAL_SENSOR1_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.1.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','29cedff7a5f043caaaa8ff5798b3e925','{#EXTERNAL_SENSOR1_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34587','20','1.3.6.1.4.1.318.1.1.25.1.2.2.7.1.1','10402','{#EXTERNAL_SENSOR2_NAME}: Humidity sensor','external.sensor.humidity[uioSensorStatusHumidity.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current humidity reading - a relative humidity
 percentage. -1 indicates an invalid reading due to either a
 sensor that doesn''t read humidity or lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','445fa35253b942cf8009460ea67701fd','{#EXTERNAL_SENSOR2_NAME}: HUMIDITY SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34588','20','1.3.6.1.4.1.318.1.1.25.1.2.2.9.1.1','10402','{#EXTERNAL_SENSOR2_NAME}: Sensor alarm status','external.sensor.status[uioSensorStatusAlarmStatus.2.{#SNMPINDEX}]','1m','7d','365d','0','3','','','','',NULL,'285','','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The alarm status of the sensor. Possible values:
uioNormal                 (1),
uioWarning                (2),
uioCritical               (3),
sensorStatusNotApplicable (4)','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','58a2e39cd7fc4fe1bd825ce6086b4931','{#EXTERNAL_SENSOR2_NAME}: SENSOR ALARM STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34589','20','1.3.6.1.4.1.318.1.1.25.1.2.2.6.1.1','10402','{#EXTERNAL_SENSOR2_NAME}: Temperature sensor','external.sensor.temperature[uioSensorStatusTemperatureDegC.2.{#SNMPINDEX}]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The sensor''s current temperature reading in Celsius.
 -1 indicates an invalid reading due to lost communications.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c78cd23b59254174b333514d9c8d28e1','{#EXTERNAL_SENSOR2_NAME}: TEMPERATURE SENSOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34590','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.6.1.1.{#PHASEINDEX}','10402','{#PHASEINDEX}: Phase input current','phase.input.current[upsPhaseInputCurrent.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input current in 0.1 amperes, or -0.1 if it''s
 unsupported by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a8ed43fa8a4543f8ab116c8886511aa3','{#PHASEINDEX}: PHASE INPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34591','20','1.3.6.1.4.1.318.1.1.1.9.2.3.1.3.1.1.{#PHASEINDEX}','10402','{#PHASEINDEX}: Phase input voltage','phase.input.voltage[upsPhaseInputVoltage.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The input voltage in VAC, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','593b355efb0a4e40bd3527c24994da0a','{#PHASEINDEX}: PHASE INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34592','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.4.1.1.{#PHASEINDEX}','10402','{#PHASEINDEX}: Phase output current','phase.output.current[upsPhaseOutputCurrent.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The output current in 0.1 amperes drawn
 by the load on the UPS, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','582f567d83e84d64862183c3b1e248f8','{#PHASEINDEX}: PHASE OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34593','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.10.1.1.{#PHASEINDEX}','10402','{#PHASEINDEX}: Phase output load, %','phase.output.load.percent[upsPhaseOutputPercentLoad.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The percentage of the UPS load capacity in VA at
 redundancy @ (n + x) presently being used on this
 output phase, or -1 if it''s unsupported by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','32c88f722f074fd699d880a603aaa91b','{#PHASEINDEX}: PHASE OUTPUT LOAD, %');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34594','20','1.3.6.1.4.1.318.1.1.1.9.3.3.1.3.1.1.{#PHASEINDEX}','10402','{#PHASEINDEX}: Phase output voltage','phase.output.voltage[upsPhaseOutputVoltage.1.1.{#PHASEINDEX}]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','2',NULL,'MIB: PowerNet-MIB
The output voltage in VAC, or -1 if it''s unsupported
 by this UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0502345887e54bbc849a9a4e46a571da','{#PHASEINDEX}: PHASE OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34595','20','1.3.6.1.4.1.318.1.1.1.2.3.1.0','10403','Battery capacity','battery.capacity[upsHighPrecBatteryCapacity]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The remaining battery capacity expressed as
 percentage of full capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','94c5c76b7e09402bb221827ee1fea5bc','BATTERY CAPACITY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34596','20','1.3.6.1.4.1.318.1.1.1.4.1.1.0','10403','Output status','output.status[upsBasicOutputStatus]','1m','7d','365d','0','3','','','','',NULL,'295','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current state of the UPS. If the UPS is unable to
 determine the state of the UPS this variable is set
 to unknown(1).
During self-test most UPSes report onBattery(3) but
 some that support it will report onBatteryTest(15).
 To determine self-test status across all UPSes, refer
 to the upsBasicStateOutputState OID.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','3170d441ede24494b9570b6d318cc05f','OUTPUT STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34597','20','1.3.6.1.2.1.1.3.0','10403','Uptime (network)','system.net.uptime[sysUpTime.0]','30s','2w','0d','0','3','','uptime','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The time (in hundredths of a second) since the network management
portion of the system was last re-initialized.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','336ef2166914449fafa13ab08fe7c7a1','UPTIME (NETWORK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34598','20','1.3.6.1.4.1.318.1.1.1.1.2.3.0','10403','Serial number','system.sn[upsAdvIdentSerialNumber]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
An 8-character string identifying the serial number of
 the UPS internal microprocessor.  This number is set at
 the factory.  NOTE: This number does NOT correspond to
 the serial number on the rear of the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','269ce166bb904fa8b11fc2fdf1f67d76','SERIAL NUMBER');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34599','20','1.3.6.1.2.1.1.2.0','10403','System object ID','system.objectid[sysObjectID.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The vendor''s authoritative identification of the network management
subsystem contained in the entity.  This value is allocated within the SMI enterprises
subtree (1.3.6.1.4.1) and provides an easy and unambiguous means for determining`what
kind of box'' is being managed.  For example, if vendor`Flintstones, Inc.'' was
assigned the subtree1.3.6.1.4.1.4242, it could assign the identifier 1.3.6.1.4.1.4242.1.1
to its `Fred Router''.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1c00c980ff284fb2bafb8358cc477d13','SYSTEM OBJECT ID');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34600','20','1.3.6.1.2.1.1.5.0','10403','System name','system.name[sysName.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
An administratively-assigned name for this managed node.By
convention, this is the node''s fully-qualified domain name.  If the name is unknown,
the value is the zero-length string.','3','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','482bec6573f249abbb721f2ec90def3b','SYSTEM NAME');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34601','20','1.3.6.1.4.1.318.1.1.1.1.1.1.0','10403','Model','system.model[upsBasicIdentModel]','15m','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS model name (e.g. ''APC Smart-UPS 600'').','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','866889bb71e949c18520bf8fefd3e7ea','MODEL');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34602','20','1.3.6.1.2.1.1.6.0','10403','System location','system.location[sysLocation.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The physical location of this node (e.g., `telephone closet,
3rd floor'').  If the location is unknown, the value is the zero-length string.','24','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d0351d1bc1dc4f1b853fe64d456b3570','SYSTEM LOCATION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34603','20','1.3.6.1.2.1.1.1.0','10403','System description','system.descr[sysDescr.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
A textual description of the entity. This value should
include the full name and version identification of the system''s hardware type, software operating-system, and
networking software.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','01302a36cafd421c90d746f785c83f3f','SYSTEM DESCRIPTION');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34604','20','1.3.6.1.2.1.1.4.0','10403','System contact details','system.contact[sysContact.0]','15m','2w','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: SNMPv2-MIB
The textual identification of the contact person for this managed
node, together with information on how to contact this person.  If no contact
information is known, the value is the zero-length string.','23','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','da60acc731a64257a90512b5c70d1e92','SYSTEM CONTACT DETAILS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34605','17','','10403','SNMP traps (fallback)','snmptrap.fallback','1m','2w','0','0','2','','','','hh:mm:sszyyyy/MM/dd',NULL,NULL,'','','0','','','','','0',NULL,'The item is used to collect all SNMP traps unmatched by other snmptrap items','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d08fb7e3fae84d2cbae64ab9771ffcdc','SNMP TRAPS (FALLBACK)');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34606','20','1.3.6.1.4.1.318.1.1.1.4.3.1.0','10403','Output voltage','output.voltage[upsHighPrecOutputVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The output voltage of the UPS system in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','6c7d7d803647478c8f2a79875457110c','OUTPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34607','20','1.3.6.1.4.1.318.1.1.1.4.3.3.0','10403','Output load','output.load[upsHighPrecOutputLoad]','1m','7d','365d','0','0','','%','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current UPS load expressed as percentage
of rated capacity.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','cd7b2c1b12df4fd19f37485aa380b295','OUTPUT LOAD');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34608','20','1.3.6.1.4.1.318.1.1.1.2.2.5.0','10403','External battery packs count','battery.external_packs_count[upsAdvBatteryNumOfBattPacks]','1h','7d','365d','0','3','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The number of external battery packs connected to the UPS. If
 the UPS does not use smart cells then the agent reports
 ERROR_NO_SUCH_NAME.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','1a52452353b443d6b965293fda3b16b9','EXTERNAL BATTERY PACKS COUNT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34609','20','1.3.6.1.4.1.318.1.1.1.4.3.4.0','10403','Output current','output.current[upsHighPrecOutputCurrent]','1m','7d','365d','0','0','','A','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current in amperes drawn by the load on the UPS.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','145d3bf81b00427aad5563a4feb7aea1','OUTPUT CURRENT');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34610','20','1.3.6.1.4.1.318.1.1.1.3.3.1.0','10403','Input voltage','input.voltage[upsHighPrecInputLineVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current utility line voltage in VAC.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','d7281586af02462a9a2f511c0a5741eb','INPUT VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34611','20','1.3.6.1.4.1.318.1.1.1.3.3.4.0','10403','Input frequency','input.frequency[upsHighPrecInputFrequency]','1m','7d','365d','0','0','','Hz','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current input frequency to the UPS system in Hz.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0ceb5a6d71f440fcbd2da06b0cc1bbb3','INPUT FREQUENCY');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34612','20','1.3.6.1.4.1.318.1.1.1.3.2.5.0','10403','Input fail cause','input.fail[upsAdvInputLineFailCause]','1m','7d','365d','0','3','','','','',NULL,'293','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The reason for the occurrence of the last transfer to UPS
battery power.  The variable is set to:
- noTransfer(1) -- if there is no transfer yet.
- highLineVoltage(2) -- if the transfer to battery is caused
by an over voltage greater than the high transfer voltage.
- brownout(3) -- if the duration of the outage is greater than
five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- blackout(4) -- if the duration of the outage is greater than five
seconds and the line voltage is between 40% of the rated
output voltage and ground.
- smallMomentarySag(5) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and the low transfer voltage.
- deepMomentarySag(6) -- if the duration of the outage is less
than five seconds and the line voltage is between 40% of the
rated output voltage and ground.  The variable is set to
- smallMomentarySpike(7) -- if the line failure is caused by a
rate of change of input voltage less than ten volts per cycle.
- largeMomentarySpike(8) -- if the line failure is caused by
a rate of change of input voltage greater than ten volts per cycle.
- selfTest(9) -- if the UPS was commanded to do a self test.
- rateOfVoltageChange(10) -- if the failure is due to the rate of change of
the line voltage.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','0a12f157ae844129a35084b5ab0a8eab','INPUT FAIL CAUSE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34613','20','1.3.6.1.4.1.318.1.1.1.2.3.4.0','10403','Battery voltage','battery.voltage[upsHighPrecBatteryActualVoltage]','1m','7d','365d','0','0','','V','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The actual battery bus voltage in Volts.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','4b456cb5c0224b31a2f8b4bb40d8203b','BATTERY VOLTAGE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34614','20','1.3.6.1.4.1.318.1.1.1.2.3.2.0','10403','Battery temperature','battery.temperature[upsHighPrecBatteryTemperature]','1m','7d','365d','0','0','','℃','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The current internal UPS temperature in Celsius.
 Temperatures below zero read as 0.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','c03e15aaf58f4056b88677c44c5d7d87','BATTERY TEMPERATURE');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34615','20','1.3.6.1.4.1.318.1.1.1.2.1.1.0','10403','Battery status','battery.status[upsBasicBatteryStatus]','1m','7d','365d','0','3','','','','',NULL,'294','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The status of the UPS batteries. A batteryLow(3) value
 indicates the UPS will be unable to sustain the current
 load, and its services will be lost if power is not restored.
 The amount of run time in reserve at the time of low battery
 can be configured by the upsAdvConfigLowBatteryRunTime.
 A batteryInFaultCondition(4)value indicates that a battery
 installed has an internal error condition.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','a631704123c2498aa8ce973e36c13698','BATTERY STATUS');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34616','20','1.3.6.1.4.1.318.1.1.1.2.2.3.0','10403','Battery runtime remaining','battery.runtime_remaining[upsAdvBatteryRunTimeRemaining]','1m','7d','365d','0','0','','s','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The UPS battery run time remaining before battery
 exhaustion.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','f151210b9cd749b2b3e5af2145733c82','BATTERY RUNTIME REMAINING');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34617','20','1.3.6.1.4.1.318.1.1.1.2.2.4.0','10403','Battery replace indicator','battery.replace_indicator[upsAdvBatteryReplaceIndicator]','1m','7d','365d','0','3','','','','',NULL,'292','','','0','','','','','0',NULL,'MIB: PowerNet-MIB
Indicates whether the UPS batteries need replacement.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','8f4351d23be04a3abee1e6edb746a9ec','BATTERY REPLACE INDICATOR');
INSERT INTO items (itemid,type,snmp_oid,hostid,name,key_,delay,history,trends,status,value_type,trapper_hosts,units,formula,logtimefmt,templateid,valuemapid,params,ipmi_sensor,authtype,username,password,publickey,privatekey,flags,interfaceid,description,inventory_link,lifetime,evaltype,jmx_endpoint,master_itemid,timeout,url,query_fields,posts,status_codes,follow_redirects,post_type,headers,retrieve_mode,request_method,output_format,verify_peer,verify_host,allow_traps,discover,uuid,name_upper) values ('34618','20','1.3.6.1.4.1.318.1.1.1.2.1.3.0','10403','Battery last replace date','battery.last_replace_date[upsBasicBatteryLastReplaceDate]','1h','7d','0','0','1','','','','',NULL,NULL,'','','0','','','','','0',NULL,'MIB: PowerNet-MIB
The date when the UPS system''s batteries were last replaced
 in mm/dd/yy (or yyyy) format. For Smart-UPS models, this value
 is originally set at the factory. When the UPS batteries
 are replaced, this value should be reset by the administrator.
 For Symmetra PX 250/500 this OID is read-only and is configurable in the local display only.','0','30d','0','',NULL,'3s','','','','200','1','0','','0','0','0','0','0','0','0','7a887ae254b04b19bac605bb36141767','BATTERY LAST REPLACE DATE');
